ATBECHDEDKESFRGBGRITLILUNLSEMCPTIESILTLVFIROMKCYALTRBGCZEEHUPLSKBAHRISYU........
J
DIM360 (Ver 1.5 21 Nov 2005) - 1100000/0
1726890
EUROPEAN PATENT APPLICATION
A1
20061129
EP
06380106.2
20060509
es
en
en
200501112
20050510
ES
20061129
200648
20061129
200648
F24F 1/00 20060101AFI20060829BHEP
F24F 13/20 20060101ALI20060829BHEP
de
Innenraumeinheit einer Klimaanlage
en
Indoor unit of an air conditioner
fr
Unité d'intérieur d'un dispositif de conditionnement d'air
3
Universitat Politecnica de Catalunya
07412590
5161EP440UPC
647 Avenida Diagonal
08028 Barcelona
ES
Nacenta Anmella, Jose Maria
647 Avenida Diagonal
08028 Barcelona
ES
SUGRANES - VERDONCES - FERREGÜELA
00101212
304 Calle Provenza
08008 Barcelona
ES
AT
BE
BG
CH
CY
CZ
DE
DK
EE
ES
FI
FR
GB
GR
HU
IE
IS
IT
LI
LT
LU
LV
MC
NL
PL
PT
RO
SE
SI
SK
TR
AL
BA
HR
MK
YU
Indoor unit of an air conditioner of the type that consists of a hollow casing with vents for the inlet and outlet of air, respectively, being housed therein at least one heat exchanger and a centrifugal fan that inhales air, through the inlet vent, from the comfort area of a room to the surfaces of the heat exchanger and returns it, through the outlet vent, to said comfort area, the indoor unit comprising a separator that divides the casing into two transversal cavities, one inlet cavity and one outlet cavity, with an opening for the air to pass from one cavity to the other, the fan being positioned in said opening with its axis of rotation essentially perpendicular to the largest faces of the casing, the opening constituting the entrance to the fan's air intake.

Technical field of the invention
The invention relates to an indoor unit of an air conditioner of the type that consists of a hollow casing with vents for the inlet and outlet of air, respectively, being housed therein at least one heat exchanger and a fan that inhales air, through the inlet vent, from the comfort area of a room to the surfaces of the heat exchanger and returns it, through the outlet vent, to said comfort area.

Background of the invention
The known indoor units of air conditioners consist of an outer casing, in the form of a cabinet, with an air inlet grille or orifice situated preferably, in apparatus to be installed in a horizontal or vertical position, on the lower part and an air outlet grille or orifice situated on the front part of the casing. Said units also comprise a heat exchanger generally consisting, in cooling apparatus, of an evaporator that cools the air that enters the casing through the inlet grille using the evaporation heat of a refrigerant. A fan housed inside the casing is responsible for inhaling the air from the room, directing it towards the heat exchanger of the indoor unit and expelling it towards the outside through the outlet grille or through tubes.
An example of an indoor unit of an air conditioner is disclosed in document WO 3033965. The casing of the unit has a front orifice or a grille that extends horizontally, behind which a tangential fan is positioned, inside the casing, which inhales and expels the air in a tangential direction in relation to its axis of rotation. Until now, this type of fan, with an axis of rotation parallel to the inlet grille or orifice, has been used because the fan motor can be housed inside the casing at one of the ends of the fan, thus increasing the length of the casing to a greater or lesser extent whilst avoiding having to increase the thickness thereof. In this type of unit the thickness of the casing is determined by the diameter of the fan wheel, which, to achieve an optimum airflow, must have a minimum size. As has been mentioned above, this minimum size conditions the thickness of the casing; the greater the airflow, the thicker the casing.
The use of centrifugal fans, positioned inside the casing in such a way that their axis of rotation is perpendicular to the largest faces of said casing, partly solves the aforementioned problems. Despite the fact that the diameter of the fan wheel does not condition the thickness of the casing, the size of the drive motor of said fans does condition said thickness. This type of fan is often used in units to be installed horizontally on the ceilings of rooms requiring air conditioning. In this type of installations the thickness of the unit is not particularly relevant as the unit is usually built into the false ceiling of the room and the formwork of the floor above.
There is therefore a need for an indoor air-conditioning unit that is thinner than known units, without this entailing a reduction in the flow of inhaled air, ensuring an optimum cooling capacity of the air conditioner.

Explanation of the invention
The indoor unit of an air conditioner that is the object of the invention overcomes the aforementioned problems. Said unit consists of an essentially parallelepipedic straight rectangular hollow casing with vents for the inlet and outlet of air, respectively, being housed therein at least one filter element, at least one heat exchanger and a centrifugal fan that inhales air, through the inlet vent, from the comfort area of a room to the surfaces of the heat exchanger and returns it, through the outlet vent, to said comfort area.
The unit is essentially characterised in that it comprises a separator that divides the casing into two transversal cavities, one inlet cavity and one outlet cavity, with an opening for the air to pass from one cavity to the other, the fan being positioned in said opening of the separator, in such a way that its axis of rotation is essentially perpendicular to the largest faces of the casing, said opening constituting the entrance to the air intake of the fan, and in that the heat exchanger is situated on one side or other of the fan, always outside the projection, in an axial direction, of the air intake thereof.
According to another characteristic of the invention, the relationship between the diameter (D) of the fan wheel and the outlet height (h) of the fan blades follows the ratio: D/h = 5.5.
According to another characteristic of the invention, the unit is characterised in that the drive motor of the fan is housed therein, and in that the stator of said motor is housed inside a casing situated in the air intake of the fan, fastened to one of the largest faces of the hollow casing of the indoor unit.
According to another characteristic of the invention, the fan wheel comprises a flat annulus or flat circle that joins the blades of said wheel, which project from the air intake towards the ends of the fan, the annulus being joined to the rotor of the drive motor of the fan, which is an external rotor motor, and in that the stator of said motor is fastened, by supports, to the face of the casing adjacent to the annulus of the fan wheel.

Brief description of the drawings
In the attached drawings an embodiment of the indoor unit of an air conditioner according to the invention is illustrated by means of a non-limiting example. In said drawings:
- Fig. 1 is a view of the longitudinal section of an indoor unit according to the invention;
- Figs. 2a, 2b and 2b each show cross-section views of the separator and the fan corresponding to three variants of an indoor unit according to the invention; and
- Fig. 3 shows a schematic perspective view of the indoor unit shown in Fig. 1.

Detailed description of the drawings
The indoor unit 1 of the air conditioner shown by way of an example in Fig. 1 is formed in a known way by a parallelepipedic straight rectangular hollow casing 2 with vents for the inlet 18 and outlet 19 of air, respectively, being housed therein two filter elements 3, that cover said air inlet and outlet vents; a heat exchanger 4; and a centrifugal fan 5 that inhales air, through the inlet vent 18, from the comfort area of a room to the surfaces of the heat exchanger 4 and returns it, through the outlet vent 19, to said comfort area.
As is shown in Figs. 1 and 3, the indoor unit 1 comprises a separator 6 that divides the casing into two transversal cavities, one inlet cavity 1 a and one outlet cavity 1 b. The separator has an opening 11 (see Fig. 3) for the air to pass from the inlet cavity 1 a to the outlet cavity 1b, always through the centrifugal fan 5 positioned for this purpose on one side of said opening in the separator, its axis of rotation being perpendicular to the largest faces 17 and 17' of the casing 2, said opening 11 constituting the fan's air intake 7. In the example shown in Figs. 1 and 3 the heat exchanger 4 is situated in the inlet cavity 1 a of the casing 2, outside the projection, in an axial direction, of the fan's air intake 7.
The air flow through the inside of the casing 2 follows an axial direction at the inlet of the fan 5 and flows perpendicular to the axis thereof at the outlet of the fan 5, the inlet direction and outlet direction of the air thus forming a right angle.
The fan 5 is preferably of the type fitted with blades 9 facing forwards (action) or backwards (reaction). Fans fitted with blades facing forwards have a larger number of blades but generate little noise. For the same speed of rotation, this type of fan achieves the same airflow with a smaller fan compared to other types of fan. Fans fitted with blades facing backwards offer better performance than the former type because the old flat blades can be replaced by the latest designs with an aerodynamic profile, making it possible to reach performances of between 75 and 80% although, for the same speed of rotation and number of blades, their mass flow rate and their pressure are lower than fans of the type that have blades facing forwards.
In general, by using this type of fans it is not necessary to reach high speeds of rotation to achieve sufficient flow and force of air. In this embodiment the fan works at few revolutions per minute; to be specific, with a motor with 6 or more poles it can work at up to 950 revolutions per minute.
In order to achieve the optimum flow with the minimum space in which to locate the drive motor of the fan 5, the relationship between the diameter D of the wheel 8 of the fan 5 and the outlet height h of the fan blades 9 follows the expression D/h = 5.5. It is thus possible to achieve, as can be seen in Fig. 3, a considerable reduction in the thickness of the casing 2 compared to the current thickness of known indoor units, keeping the same technical features as regards cooling capacity, airflow, available pressure, electrical consumption and noise level. This reduction is actually due to not only the dimensions of the fan 5 but also the innovative location of the drive motor 12 inside the air intake 7 of the fan 5. With these characteristics it is possible to reduce the maximum thickness of the casing of conventional indoor units of air conditioners by between 30 and 40%.
In effect, as can be observed in detail in Figs. 2 and 3, the stator 10 of the drive motor 12 is housed inside a casing 13 situated in the air intake 7 of the fan 5, fastened to one of the largest faces of the hollow casing 2 of the indoor unit. With the motor thus located, the thickness of the casing 2 adapts to measurements very similar to those of the drive motor 12, which in turn guarantees an airflow of the proportions between the diameter and the outlet height of the blades of the fan described above.
As can be observed in Figs. 2a and 2b the wheel 8 of the fan 5 comprises a flat annulus 15 that joins the blades 9 of said wheel, which project from the annulus towards the air intake 7, said annulus 15 being joined to the rotor 14 of the drive motor 12 of the fan 5. In the example in Fig. 2b, the drive motor 12 is an internal rotor motor, and the stator 10 of said motor is fastened, by corresponding supports 16', to the face 17' opposite the face 17 of the casing 2 that is adjacent to the annulus 15 of the fan wheel.
By way of an alternative, in the example shown in Fig. 2a the drive motor 12 is an external rotor motor, and the stator 10 of said motor is fastened, by supports 16, to the face 17 of the casing 2 adjacent to the annulus 15 of the wheel 8 of the fan 5. This has an advantage over the previous variant, in that the supports 16 do not have to be adapted to the thickness of the casing 2.
Fig. 2c shows another variant of an indoor unit of an air conditioner according to the invention, and more specifically of the separator 6 and the area in which the wheel 8 is located. In said variant it can be observed that the face 17 of the casing 2 is not flat and that, unlike the variants in Figs. 2a and 2b, it has a recess 20 that determines a housing wherein the drive motor 12 of the fan 5 is located. Said motor 12 is firmly attached to the casing by means of supports 16' and it also has a second set of wall fastening supports 21 for the attachment thereof to the walls of the room, preferably to the wall adjacent to the ceiling.
In the example shown in Fig. 2c, the recess 20 takes the form of an inverted dome and has a hole through which the axis of rotation of the fan 5, driven by the rotor 14 of the drive motor 12 is inserted into the casing 2 to thereby transmit the rotational movement to the wheel 8 of the fan 5. Advantageously, according to this constructive variant it is not necessary to dismantle the casing 2 to perform any maintenance or repair work on the drive motor 12.
Unlike known indoor units, wherein the fan 5 has its own casing that encloses the fan wheel and forms the fan's air intake, in the indoor unit according to the invention it is the separator 6 that performs said function. As can be observed in Fig. 1, the opening 11 in the separator 6 has a section, like a funnel, that widens in the direction of the airflow. In said figure, the walls that constitute the air intake of the fan 5, which form part of the separator 6, are of a concave generatrix whilst the upper profile of the blade 9 is straight. Although not shown in the drawings, it should be understood that the upper profile of the blades 9 can be curved and that the walls that constitute the air intake of the fan 5 can have a straight generatrix or can have a curvature that is complementary to that of the upper profile of the blades 9.
In Figs. 2a and 2b, by way of an alternative, the opening 11 in the separator 6 does not have a collar to accompany the air inhaled by the fan 5 towards the blades 9.
On the outlet side, the separator 6 can have a rounded form to aid the flow of air as it leaves the fan 5, towards the outlet vent 19, similar to spiral-shaped casings.
Naturally, the air inlet 18 and outlet 19 vents can be situated on the lateral faces or on the front face of the casing 2. As regards the heat exchanger 4, it is disposed at an angle to the largest faces 17 and 17' of the casing 2 of the indoor unit 1, thus maximising the surface area for contact with the air.
With these characteristics, the indoor unit 1 of the air conditioner that is the object of the invention can either be installed in a horizontal position, suspended from the ceiling of the room to be air conditioned, or in a vertical position, resting against one of the walls of said room, occupying a minimum space thanks to the reduction in the thickness of the casing 2.
1. Indoor unit (1) of an air conditioner of the type that consist of an essentially parallelepipedic straight rectangular hollow casing (2) with vents for the inlet (18) and outlet (19) of air, respectively, being housed therein at least one filter element (3), at least one heat exchanger (4) and a centrifugal fan (5) that inhales air, through the inlet vent, from the comfort area of a room to the surfaces of the heat exchanger and returns it, through the outlet vent, to said comfort area, characterised in that it comprises a separator (6) that divides the casing into two transversal cavities, one inlet cavity (1a) and one outlet cavity (1 b), with an opening (11) for the air to pass from one cavity to the other, the fan being positioned in said opening of the separator, in such a way that its axis of rotation is essentially perpendicular to the largest faces of the casing, said opening constituting the air intake (7) of the fan, and in that the heat exchanger is situated on one side or other of the fan, always outside the projection, in an axial direction, of the air intake thereof.
2. Indoor unit (1) according to claim 1, characterised in that the relationship between the diameter (D) of the fan wheel (8) and the outlet height (h) of the fan blades (9) follows the ratio:
D
/
h
=
5.5
3. Indoor unit (1) according to the previous claims, characterised in that the drive motor (12) of the fan (5) is housed therein, and in that the stator (10) of said motor is housed inside a casing (13) situated in the air intake (7) of the fan and is fastened to one of the largest faces of the hollow casing (2) of the indoor unit.
4. Indoor unit (1) according to claim 3, characterised in that the fan wheel (8) comprises a flat annulus (15) that joins the blades (9) of said wheel, which project from the air intake towards the ends of the fan (7), the annulus being joined to the rotor (14) of the drive motor (12) of the fan (5), which is an external rotor motor, and in that the stator (10) of said motor is fastened to the face (17) of the casing (2) adjacent to the annulus of the fan wheel by supports (16).

REFERENCES CITED IN THE DESCRIPTION
This list of references cited by the applicant is for the reader's convenience only. It does not form part of the European patent document. Even though great care has been taken in compiling the references, errors or omissions cannot be excluded and the EPO disclaims all liability in this regard.

Patent documents cited in the description
- WO
3033965
A
[0003]