ATBECHDEDKESFRGBGRITLILUNLSEMCPTIESILTLVFIROMKCYALTRBGCZEEHUPLSK..HRIS..MTNORS..SM..................
J
BDM Ver 1.7.2 (20 November 2019) - 2100000/0
3648126
EUROPEAN PATENT SPECIFICATION
B1
20210825
EP
18203718.4
20181031
20200915
en
en
en
20210825
202134
20200506
202019
20210825
202134
20210316
H01F 27/28 20060101AFI20190418BHEP
H01F 27/34 20060101ALI20190418BHEP
de
ELEKTRISCHE KOMPONENTE, INSBESONDERE TRANSFORMATOR ODER INDUKTOR
en
ELECTRICAL COMPONENT, ESPECIALLY TRANSFOMER OR INDUCTOR
fr
COMPOSANT ÉLECTRIQUE, NOTAMMENT TRANSFORMATEUR OU INDUCTEUR
WO-A1-2012/017616
WO-A1-2018/007514
US-A- 3 774 135
Gradinger, Thomas
Birkenweg 3
5032 Aarau Rohr
CH
Drofenik, Uwe
Buchzelgstrasse 37
8053 Zürich
CH
ABB Power Grids Switzerland AG
101843910
AD2133 EP S5
Bruggerstrasse 72
5400 Baden
CH
Vossius & Partner Patentanwälte Rechtsanwälte mbB
101508488
P.O. Box 86 07 67
81634 München
DE
AL
AT
BE
BG
CH
CY
CZ
DE
DK
EE
ES
FI
FR
GB
GR
HR
HU
IE
IS
IT
LI
LT
LU
LV
MC
MK
MT
NL
NO
PL
PT
RO
RS
SE
SI
SK
SM
TR

TECHNICAL FIELD
Embodiments of the present disclosure relate to electrical components having a winding arrangement for high voltage applications. In particular, embodiments of the present disclosure relate to transformers, particularly oil-immersed transformers or dry-cast medium-frequency transformers (MFTs), and inductors.

BACKGROUND
Medium-frequency transformers (MFTs) are key components in various power-electronic systems. Examples in rail vehicles are auxiliary converters and solid-state transformers (SSTs) replacing the bulky low-frequency traction transformers. Further applications of SSTs are being considered, for example for grid integration of renewable energy sources, electrical vehicle (EV) charging infrastructure, data centers, or power grids on board of ships. It is expected that SSTs will play an increasingly important role in the future.
Due to operating frequencies in the range of tens of kHz, MFT windings are often made from litz wires or foils to keep skin- and proximity-effect losses within tolerable limits.
As soon as two or more litz wires or foils are connected in parallel, there is a risk of circulating currents among the wires introduced by a magnetic flux. These currents have the potential of strongly, e.g. by a factor of 2, increasing the winding losses beyond those just caused by skin and proximity effect at the level of individual wires or foils.
The same problems appears in inductors having a plurality of parallel connected conductors, for example litz wires or foils.
Thus, there is a need of a solution that reduces the circulating current in parallel circuits of conductors in electrical components. Careful winding design is needed to avoid those circulating currents.

SUMMARY
In light of the above, an electrical component, especially a transformer or an inductor, is provided. Further aspects, advantages, and features are apparent from the dependent claims, the description, and the accompanying drawings.
According to the invention as defined in claim 1 an electrical component comprises a ferromagnetic core with a first and a second leg; a primary winding with a first primary winding portion arranged around the first leg of the ferromagnetic core and a second primary winding portion arranged around the second leg of the ferromagnetic core; wherein the first primary winding portion and the second primary winding portion each comprise a plurality of conductors connectable in parallel and arranged around the ferromagnetic core in a cross section with the conductors being radially displaced with respect to each other at radial row positions, wherein the number of conductors of the first primary winding portion is equal the number of conductors of the second primary winding portion and each of the conductors of the first primary winding portion is connected in series with one corresponding conductor of the second primary winding portion, whereby a conductor of a radially outer row of the first primary winding portion is connected in series with a conductor of a radially inner row of the second primary winding portion, thereby reducing the sum of the magnetic flux between parallel connectable conductors of the first primary winding portion and parallel connectable conductors of the second primary winding portion.
Accordingly, the design of the electrical component of the present disclosure is improved compared to conventional structure of this kind of electrical components. In particular, the reduction of the sum of the magnetic flux or the total magnetic flux of the primary winding between parallel connectable conductors of the first and second primary winding portions is with respect to a situation in which the conductor of a radially outer row of the first primary winding portion is connected in series with a conductor of a radially outer row of the second primary winding portion. In other words, a transposition of the radial conductor position on the first leg with respect to the radial conductor position on the second leg is suggested.
The term "connectable in parallel" describing the conductors should be understood in that the conductors are not electrically connected in series. Furthermore, the conductors can be separated from each other by, for example, an isolator. Typical conductors are, for example, litz wires arranged in a cable formed of a group of litz wires or foils arranged as a stack of layers. It should be understood that connectable in parallel does not necessarily mean the conductors form an electrical parallel circuit inside the device. The actual electrical connection of the parallel conductors can be a part of the electrical component or can be externally within a suitable usage of the electrical component. Connectable in parallel should be understood as at least connectable in an electrical parallel circuit.
The arrangement of the primary winding with a first primary winding portion arranged around the first leg of the ferromagnetic core and a second primary winding portion arranged around the second leg of the ferromagnetic core is also known as core-type, for example, in core-type transformers
The plurality of parallel connectable conductors are arranged around the ferromagnetic core in a cross section with the conductors being radially displaced with respect to each other at radial row positions. In other words, the conductors surround the first or second leg, respectively, at different radii. Due to the different radii, there is a magnetic flux in axial direction of the first and second primary winding portion, or, in other words, between the radially inner and outer conductors. This flux - if uncompensated - induces a circulating current between the radially inner and outer conductors.
According to an aspect, the first and second primary winding portions can comprise a plurality of turns of the conductors around the first or second leg of the ferromagnetic core. The cross section of the conductors is equal in each turn. Turns can be arranged radially or radially and axially as a spiral or helix.
According to an aspect, the conductors of the first and second primary winding portions are foils. The foils can be arranged in a stack of foils and the stack can be arranged around the ferromagnetic core. The parallel connectable foils of the first primary winding portion are connected with the parallel connectable foils of the second primary winding portion, whereby a foil of a radially outer row of the first primary winding portion is connected in series with a conductor of a radially inner row of the second primary winding portion. This transposition between the two series-connected primary winding portions results in opposed magnetic fluxes which in a sum cancel each other or at least significantly reduce the total magnetic fluxes.
According to an aspect, the first primary winding portion and the second primary winding portion each comprise at least 3 conductors. In some embodiments, the second primary winding portion each comprise 4 or 6 conductors.
Preferably, the plurality of conductors of the first primary winding portion each are continually single-piece conductors. Accordingly, the plurality of conductors of the second primary winding portion each are continually single-piece conductors. Each conductor of the first primary winding portion can be connected in series with the corresponding conductor of the second primary winding portion by, for example, a cable lug. At an external in- or output all conductors can fit in a single cable lug for each winding portion resulting in a parallel circuit of the parallel connectable conductors.
According to an aspect, the electrical component further comprises a first external electrical connector connected in series with the conductors of the first primary winding portion and a second external electrical connector connected in series with the conductors of the second primary winding portion, wherein the first and second primary winding portions are located between the first and second external electrical connector. First and second external electrical connectors can be cable lugs.
According to an embodiment, the electrical component is a transformer and further comprises a secondary winding with a first secondary winding portion arranged around the first leg of the ferromagnetic core and a second secondary winding portion arranged around the second leg of the ferromagnetic core.
According to an embodiment, the transformer is an MTF. Typical frequencies and currents in an operational state for which the transformer can be adapted can be, for example 0.5 kHz to 50 kHz, especially 10 kHz to 20 kHz, and currents in the range of 20 A to 2000 A, especially 100 A to 2000 A.
The secondary winding can be the inner winding and the primary winding can be the outer winding. The primary winding can be a high voltage winding and the secondary winding can be a low voltage winding. According to a further development of the invention, the first and second secondary winding portions can comprise a plurality of parallel connectable conductors and each conductor of first secondary winding portion can be connected in series with a corresponding conductor of the second secondary winding portion analogously to the primary winding described herein. Alternatively, the first and second secondary winding portions can be connected in any possible way if the magnetic flux does not influence the workability of the electronic device. A low influence is typical for a LV winding.
According to another embodiment, the electrical component is an inductor.
According to an aspect, the first primary winding portion and the second primary winding portions are essentially geometrically symmetric, especially, the number of conductors in the first and second winding portions is equal, the number of radial rows in the cross section is equal, the number of axial rows in the cross section is equal, and/or the number of turns around the leg of the ferromagnetic core is equal. The more the first primary winding portion and the second primary winding portions equal each other, the more magnetic flux between parallel connectable conductors of the first and second primary winding portions can be canceled by the suggested series connection of conductors.
Axial and radial rows are defined by the axial and radial direction. The radial direction is the direction pointing from a leg of the ferromagnetic core to the primary winding portion. The axial direction is perpendicular to the radial direction is pointing along the leg of the ferromagnetic core.
A primary winding portion can comprise a plurality of turns around the leg of the ferromagnetic core, wherein the cross section of the plurality of parallel connectable conductors is essentially equal in each turn. Turns can be arranged in radial or axial direction or both. In one example, the primary winding portion comprises a plurality of parallel connectable foils with a cross section, wherein the conductors are radially displaced with respect to each other at radial row positions. The primary winding portion can comprise, for example, 10 turns in a radial direction. In each turn, the cross section of the foils is essentially equal, meaning the radial row position of each foil is constants with respect to each other. In another example, the primary winding portion comprises a plurality of parallel connectable litz wires. The primary winding portion comprises, for example, 10 turns arranged in axial direction, so that the cable formed of the group of litz wires forms a spiral. In each turn, the cross section of the cable is essentially equal, meaning the radial row position and the axial row position of each litz wire inside the cable is constants with respect to each other.
According to an embodiment, the first primary winding portion and the second primary winding portion each comprise a cable formed of a plurality of litz wires, wherein the plurality of parallel connectable conductors are a plurality of parallel connectable litz wires. A conductor is identified as a litz wire. Litz wires typically consists of multiple strands insulated electrically from each other. The strands are typically twisted. Each strand can have a diameter of, for example, 0.2 mm and the litz wire can consist of more than 100 litz wire strands. The litz wire can have an essentially rectangular cross section of, for example, 6mm x 12 mm.
Preferably, the plurality of parallel connectable conductors are arranged around the ferromagnetic core in a cross section with the conductors being radially displaced with respect to each other at radial row positions, wherein the radial positions, and typically also the axial positions, remain unchanged along the length of the first or second primary winding portion, In the example of litz wires, which is are grouped in a cable, the litz wires are not twisted. A cable can contain a plurality of litz wires, for example, 4 or 6 litz wires. Thus, a cross section of the plurality of litz wires remains constant, so that a litz wire, which is, for example, located radially outside in the primary winding, remains radially outside along the full length of the first or second primary winding portion.
According to an embodiment, the first primary winding portion and the second primary winding portion each are essentially helical symmetric. The cross section of the plurality of parallel connectable conductors winds around a central axis. The first primary winding portion and the second primary winding portion each can have an essentially cylindrical shape.
According to another embodiment, the first primary winding portion and the second primary winding portion each can have an essentially spiral symmetry The first primary winding portion and the second primary winding portion can have a spiral or helical symmetry. The cross section of the plurality of parallel connectable conductors winds around a central axial axis. The cross section can also wind along the central axial axis, for example, if the conductors are litz wires.
According to an aspect, each of the plurality of parallel connectable conductors has a defined radial and possibly axial position in the cross section of conductors over the full length of the first and/or second primary winding portion. In other word, there are no radial or axial transpositions of conductors inside the first and/or second primary winding portion.
The first and second primary winding portions can be formed by litz wires arranged as a closed packed spiral around the first and second leg of the ferromagnetic core, respectively.
According to this embodiment or other embodiments in which also axial rows of conductors exist in the cross section, additional radial flux can occur in the parallel connectable conductors because the H-field has a radial component near the axial top and bottom end of the first and second primary winding portion. The radial flux is typically smaller than the axial flux. However, the radial H-component is asymmetric, pointing e.g. radially outward at the top of an axial direction of the first and second primary winding portion and inward at the bottom or vice versa. In contrast, the axial H-component is symmetric, pointing in the same direction, e.g. vertically up at the top and at the bottom. Hence, the radial components of the resulting flux will cancel each other without a transposition.
According to an embodiment, the cable comprises 4 litz wires, wherein the litz wires of the first and second primary winding portions are arranged in the cable around the ferromagnetic core in a cross section comprising 2 radial rows and 2 axial rows, wherein an axial direction defines an axial top row and an axial bottom row. A litz wire of a top row of the first primary winding portion is connected in series with a litz wire of a top row of the second primary winding portion and a litz wire of a bottom row of the first primary winding portion is connected in series with a litz wire of a bottom row of the second primary winding portion.
A cable comprising a plurality of litz wires with 4 litz wires can be typically used in applications wherein in an operating state, a current of at least 100 A, typically more than 300 A, flow through the first and second primary winding portions.
According to another aspect, the cross section of the plurality of conductors can comprise 3 or more axial rows. This introduces an additional radial flux, if the conductors are not transposed axially, because the magnitude of the radial flux decreases in axial direction from an end of the primary winding towards the middle. Thus, according to an embodiment the litz wires, or other type of conductors, of the first and second primary winding portions are arranged around the ferromagnetic core in a cross section comprising K ≥ 3 axial rows of litz wires. Each row is arranged at an axial row position, wherein an axial end row position is row position number 1 and an opposite axial end row position is row position number K, wherein each litz wire in the k row position of the first primary winding portion with 1 ≤ k ≤ K is in series connected with a litz wire in the K + 1 - k row position of the second primary winding portions. This reduces the sum of the magnetic flux between parallel connectable litz wires of the first and second primary winding portions.

BRIEF DESCRIPTION OF THE DRAWINGS
So that the manner in which the above recited features of the present disclosure can be understood in detail, a more particular description of the disclosure, briefly summarized above, may be had by reference to embodiments. The accompanying drawings relate to embodiments of the disclosure and are described in the following:
Fig. 1
shows a schematic view of an electrical component, especially a transformer, according to embodiments described herein;
Fig. 2
shows a detailed schematic sectional view of a primary winding portion in a cross section according to embodiments described herein;
Fig. 3
shows a detailed schematic sectional view of a primary winding portion in a cross section according to another embodiment;
Figs. 4A and 4B
show different embodiments of primary and secondary winding portions around a leg of a ferromagnetic core according to the present disclosure;
Figs. 5A and 5B
show a schematic diagram of the flux in a primary winding portion and the series connection of conductors of the first and second primary winding portion according to an embodiment; and
Figs. 6A and 6B
show another schematic diagram of the flux in a primary winding portion and the series connection of conductors of the first and second primary winding portion according to another embodiment.

DETAILED DESCRIPTION OF EMBODIMENTS
Reference will now be made in detail to the various embodiments, one or more examples of which are illustrated in each figure. Each example is provided by way of explanation and is not meant as a limitation. For example, features illustrated or described as part of one embodiment can be used on or in conjunction with any other embodiment to yield yet a further embodiment. as long as it falls under the scope of the appended set of claims.
Within the following description of the drawings, the same reference numbers refer to the same or to similar components. Generally, only the differences with respect to the individual embodiments are described. Unless specified otherwise, the description of a part or aspect in one embodiment can apply to a corresponding part or aspect in another embodiment as well.
With exemplary reference to Fig. 1, an electrical component is shown. The electrical component of Fig. 1 is a transformer according to an embodiment, which can be combined with other embodiments described herein. Especially according to other embodiments, the electrical component can be an inductor. The electrical component comprises: a ferromagnetic core 10 with a first and a second leg 11, 12; a primary winding 20 with a first primary winding portion 21 arranged around the first leg 11 of the ferromagnetic core and a second primary winding portion 22 arranged around the second leg 12 of the ferromagnetic core; wherein the first primary winding portion 21 and the second primary winding portion 22 each comprise a plurality of parallel connectable conductors 1, 2, 3, 4, 5, 6 arranged around the ferromagnetic core in a cross section with the conductors being radially displaced with respect to each other at radial row positions, wherein the number of conductors 1, 2, 3, 4, 5, 6 of the first primary winding portion 21 is equal the number of conductors 1, 2, 3, 4, 5, 6 of the second primary winding portion 22 and each of the conductors 1, 2, 3, 4, 5, 6 of the first primary winding portion 21 is connected in series with one corresponding conductor 1, 2, 3, 4, 5, 6 of the second primary winding portion 22, whereby a conductor 1, 2, 3, 4, 5, 6 of a radially outer row of the first primary winding portion 21 is connected in series with a conductor 1, 2, 3, 4, 5, 6 of a radially inner row of the second primary winding portion 22, thereby reducing the sum of the magnetic flux between parallel connectable conductors 1, 2, 3, 4, 5, 6 of the first primary winding portion 21 and parallel connectable conductors 1, 2, 3, 4, 5, 6 of the second primary winding portion 22.
The electrical component of Fig. 1 is a transformer and further comprises a secondary winding 30 with a first secondary winding portion 31 arranged around the first leg 11 of the ferromagnetic core and a second secondary winding portion 32 arranged around the second leg 12 of the ferromagnetic core. Primary and secondary winding are separated by an insulation.
Because of insulation, the primary winding portions 21/22 are kept at larger distances from the secondary winding portions 31/32 and the ferromagnetic core 10 than the distance between secondary winding portions 31/32 and ferromagnetic core 10. The insulation distances are schematically shown in Figure 1. This reduces the height of the primary winding portions 21/22 compared to that of the secondary winding portions 31/32. Given the reduced height, the radial thickness of the primary winding 20 must be greater than that of the secondary winding 30 to provide sufficient conductor cross-section. Therefore, each primary winding portion 21, 22 has two or more rows of conductors radially displaced with respect to each.
The ferromagnetic core 10 is adapted for a core type transformer. The shape of the ferromagnetic core 10 can comprise, for example, a C-C, U-U, U-I or an L-L shape, wherein the two components form a ring with an "O"-shape. The ferromagnetic core has at least two legs 11, 12, wherein the legs 11, 12 do not have to be necessary parallel to each other, although it is preferred. Each leg 11, 12 define a separate space for a first primary winding portion 21 and a second primary winding portion 22, so that first and second primary winding portions 21, 22 do spatially not overlap.
According to yet another embodiment, the electrical component can also be an inductor. Typically, inductors only have a primary winding 20. A secondary winding 30 is not needed.
The electrical component can comprise a first external electrical connector 41 in series connected with the conductors 1, 2, 3, 4, 5, 6 of the first primary winding portion 21 and a second external electrical connector 42 in series connected with the conductors 1, 2, 3, 4, 5, 6 of the second primary winding portion 22, wherein the first and second primary winding portions 21, 22 are located between the first and second external electrical connector 41, 42 as shown in Fig. 1. All conductors 1, 2, 3, 4, 5, 6 can be connected in series with the external electrical connector 41, 42, thereby creating a parallel circuit of the conductors 1, 2, 3, 4, 5, 6.
In Fig. 1, the first and second primary winding portions 21, 22 are arranged as outer windings and the first and second secondary winding portions 31, 32 are arranged as inner windings. Preferably, first and second primary winding portions 21, 22 are both either inner or outer windings. Symmetry of first and second primary winding portions 21, 22 is preferred because the magnetic flux cancels each other best if the magnetic flux norm is equal and if the magnetic flux points in the opposite direction.
According to an embodiment, primary winding 20 is an outer winding and a HV winding. The secondary winding 30 is an inner winding and a LV winding.
Figs. 2 and 3 show two different embodiments of parallel connectable conductors arranged in a cross section. A cross section of the first or second primary winding portion 21, 22 is shown. Typically, first and second primary winding portion 21, 22 have the same structure. Fig. 2 and 3 show a more detailed structure of, for example, the left part of the first primary winding portion 21 shown in Fig. 1.
In Fig. 2, the conductors 1, 2, 3, 4 are foils. The foils 1, 2, 3, 4 are arranged in a cross section. In the embodiment of Fig. 2, the primary winding portion 21 comprises 2 turns, therefore, the cross section is shown two times. The radial position of the foils 1, 2, 3, 4 in the two cross sections is identical.
According to another embodiment shown in Fig. 3, the, conductors 1, 2, 3, 4 are litz wires. The litz wires 1, 2, 3, 4 are arranged in a cable formed of a group of litz wires. The cable has a cross section as shown in Fig. 3. The first primary winding portion 21 comprises several turns of the cable arranged as a spiral. The cross section is essential identical in each turn, especially, radial and axial position of each litz wire is 1, 2, 3, 4 is identical in each cross section. There is no transposition of conductors 1, 2, 3, 4 within a primary winding portion 21, 22. The series connection of conductors 1, 2, 3, 4 of the first and second primary winding portion 21, 22 is further described in Figs. 5A to 6B.
In the embodiment of Fig. 3, the first primary winding portion 21 comprises several turns of the litz wires arranged as a spiral. According to other embodiments, the first primary winding portion 21 can comprise one or more further radial turns of the cable forming an inner and outer spiral or several spirals radially displaced within each other. Accordingly, the second primary winding portion 22 can have the same structure.
Figs. 4A and 4B show different embodiments of the first primary and secondary winding portions 21, 31 arranged around a leg 11 of a ferromagnetic core 10 according to embodiments. The electrical component in this embodiment is a transformer and further comprises a secondary winding 30 with a first secondary winding portion 31 arranged around the first leg 11 of the ferromagnetic core and a second secondary winding portion 32 arranged around the second leg 12 of the ferromagnetic core (not shown). In Fig. 4A, primary winding 20 is an outer winding and secondary winding 30 is an inner winding. Accordingly, first secondary winding portion 31 is arranged radially closer to the first leg 11 of the ferromagnetic core 10 than first primary winding portion 21, which is arranged around the first secondary winding portion 31.
In Figs. 4A and 4B first primary winding portion 21 comprises schematically 2 turns to keep the figure simple. However, first and primary winding portion 21, 22 can comprise several turns, for example between 10 and 20.
In Fig. 4B, primary winding 20 is an inner winding and secondary winding 30 is an outer winding. Therefore, first primary winding portion 21 is arranged radially closer to the first leg 11 of the ferromagnetic core 10 than first secondary winding portion 31. However, independent of which winding 20, 30 is an inner winding, usually first and second primary winding portions 21, 22 are equal, namely either both inner or both outer winding portions.
Between primary and secondary winding 20, 30, there is a magnetic stray field, pointing in axial direction of the windings 20, 30, which is perpendicular to the shown cross sectional view in Fig. 4B. According to Ampère's law, the field increases from zero outside the windings 20, 30 to a maximum between the windings 20, 30. Within the inner winding, it increases in radial direction from zero to the maximum. Within the outer winding, it decreases back to zero. Moving radially outward in the inner winding, there is a normalized field strength of 1 after the first foil 1, of 2 after the second foil 2, etc. According to the present invention, the foils are transposed between the first and second primary winding portion 21, 22 such that the magnetic flux through loops formed by the parallel connectable foils 1, 2, 3 cancel or is at least significantly reduced.
In the embodiment of Figs. 4A /4B, foil 1 is the radially innermost foil, foil 3 is the radially outermost foil, and foil 2 is located in between. In general, a conductor 1, 2, 3, 4, 5, 6 of a radially outer row of the first primary winding portion 21 is connected in series with a conductor 1, 2, 3, 4, 5, 6 of a radially inner row of the second primary winding portion 22. Therefore at least two foils have to be transposed.
According to an embodiment, first and second primary winding portions 21, 22 are arranged around the ferromagnetic core in a cross section comprising M rows of conductors 1, 2, 3, 4, 5, 6, each row being arranged at a radial row position, with the radially innermost row position being row position number 1 and the radially outermost row position being row position number M, wherein each conductor 1, 2, 3, 4, 5, 6 in the m row position of the first primary winding portion with 1 ≤ m ≤ M is in series connected with a conductor 1, 2, 3, 4, 5, 6 in the M + 1 - m row position of the second primary winding portion. According to the numbering in Fig. 4A/4B, foils 1 and 3; 2 and 2; and 3 and 1 of the first and second primary winding portions 21, 22, respectively, are connected in series.
According to an embodiment, first primary winding portion 21 and the second primary winding portion 22 each comprise a cable formed of a group of litz wires 1, 2, 3, 4, 5, 6.
Fig. 5A shows the magnetic flux in the first and second primary winding portion 21, 22. The axial direction (z) is shown in Fig. 5A from bottom to the top and the radial direction (r) is shown from left to right. The flux has an axial component (Hz) and a radial component (Hr). Axial flux occurs because of a difference in radial distance to the ferromagnetic core 10 and the first and second secondary winding portions 31, 32. In Fig. 5A, the flux is shown upside down so that it points in the same direction. The conductors 1, 2, 3, 4 are arranged in a helix and form first and second primary winding portions 21, 22.
Fig. 5B illustrates the magnetic flux in axial (upper part of the figure) and radial (lower part of the figure) component between parallel connectable conductors of the first and second primary winding portion 21, 22. As illustrated, the magnetic flux points in different directions indicated as plus and minus. The magnetic flux is anti-symmetric. Fig. 5B also shows the connection of the conductors 1, 2, 3, 4 between first and second primary winding portion 21, 22.
In this embodiment, the litz wires 1, 2, 3, 4 of the first and second primary winding portion 21, 22 are connected such that wires 1 and 4 exchange position, and wires 2 and 3 exchange position as shown in Figs 5A/5B with the litz wires 1 and 2 being at inner row positions and litz wires 3 and 4 being at outer row positions. The exchange of position between radially inner and outer litz wires 1, 2, 3, 4 does not necessarily include an exchange between top and bottom litz wires 1, 2, 3, 4. In other words, wires 1 and 4 are at the bottom in both primary windings portions 21, 22, while wires 2 and 3 are at the top in both primary windings portions. This serial connection leads to a complete cancellation of axial and radial magnetic flux between all loops formed by the 4 parallel litz wires 1, 2, 3, 4. Therefore, circulating currents due to such fluxes are eliminated.
Figs, 6A and 6B show another embodiment, wherein the primary winding comprises six conductors 1, 2, 3, 4, 5, 6. Compared to the embodiment of Fig. 5A, the embodiment of Fig 6A comprises two additional conductors 5, 6. The conductors 1, 2, 3, 4, 5, 6 are arranged in a cross section with two radial rows and three axial rows. Conductors 1, 2 and 3 are located at radially inner positions and conductors 4, 5 and 6 are located at radially outer positions in the cross section of conductors. The compensation of axial fluxes works like in Figs. 5A and 5B. The compensation of radial fluxes doesn't work perfectly anymore, if there is no transposition in axial direction. This is because the magnitude of radial flux decreases in axial direction from the end of the primary winding towards the middle. The flux is sketched in Figs. 6A. The right side of Fig. 6A is shown upside down analog to Fig. 5A. For example, at the bottom of the first primary winding portion 21, the radial flux between litz wires {1, 6} and litz wires {2, 5} is larger than the radial flux between litz wires {2, 5} and litz wires {3, 4}. This is indicated by the change of angle of the H- field vector.
According to this embodiment, the cross section of conductors comprises K ≥ 3 axial rows of litz wires 1, 2, 3, 4, 5, 6 as shown in Fig. 6A. Each row is arranged at an axial row position, wherein an axial end row position is row position number 1 and an opposite axial end row position is row position number K, wherein each litz wire 1, 2, 3, 4, 5, 6 in the k row position of the first primary winding portion 21 with 1 ≤ k ≤ K is in series connected with a litz wire 1, 2, 3, 4, 5, 6 in the K + 1 - k row position of the second primary winding portions 22, thereby reducing the sum of the magnetic flux between parallel connectable litz wires 1, 2, 3, 4, 5, 6 of the first and second primary winding portions 21, 22.
Fig. 6B shows the serial connection of the conductors 1, 2, 3, 4, 5, 6 of the first and second primary winding portion 21, 22. Fig. 6B also illustrates the magnetic flux in radial component between parallel connectable conductors of the first and second portions 21, 22.

REFERENCE NUMBERS
1
conductor
2
conductor
3
conductor
4
conductor
5
conductor
6
conductor
10
ferromagnetic core
11
first leg
12
second leg
20
primary winding
21
first primary winding portion
22
second primary winding portion
30
secondary winding
31
first secondary winding portion
32
second secondary winding portion
41
first external electrical connector
42
second external electrical connector
1. An electrical component, comprising:
a ferromagnetic core (10) with a first and a second leg (11, 12);
a primary winding (20) with a first primary winding portion (21) arranged around the first leg (11) of the ferromagnetic core and a second primary winding portion (22) arranged around the second leg (12) of the ferromagnetic core;
wherein the first primary winding portion (21) and the second primary winding portion (22) each comprise a plurality of conductors (1, 2, 3, 4, 5, 6) connectable in parallel and arranged around the ferromagnetic core in a cross section with the conductors being radially displaced with respect to each other at radial row positions, wherein the number of conductors (1, 2, 3, 4, 5, 6) of the first primary winding portion (21) is equal the number of conductors (1, 2, 3, 4, 5, 6) of the second primary winding portion (22) and
each of the conductors (1, 2, 3, 4, 5, 6) of the first primary winding portion (21) is connected in series with one corresponding conductor (1, 2, 3, 4, 5, 6) of the second primary winding portion (22), whereby a conductor (1, 2, 3, 4, 5, 6) of a radially outer row of the first primary winding portion (21) is connected in series with a conductor (1, 2, 3, 4, 5, 6) of a radially inner row of the second primary winding portion (22), thereby reducing the sum of the magnetic flux between parallel connectable conductors (1, 2, 3, 4, 5, 6) of the first primary winding portion (21) and parallel connectable conductors (1, 2, 3, 4, 5, 6) of the second primary winding portion (22).
2. The electrical component according to claim 1, wherein the electrical component is an inductor.
3. The electrical component according to claim 1, wherein the electrical component is a transformer and further comprises a secondary winding (30) with a first secondary winding portion (31) arranged around the first leg (11) of the ferromagnetic core and a second secondary winding portion (32) arranged around the second leg (12) of the ferromagnetic core.
4. The electrical component according to any of the preceding claims, wherein the first and second primary winding portions (21, 22) are arranged around the ferromagnetic core in a cross section comprising M rows of conductors (1, 2, 3, 4), each row being arranged at a radial row position, with the radially innermost row position being row position number 1 and the radially outermost row position being row position number M, wherein each conductor (1, 2, 3, 4) in the m^{th} row position of the first primary winding portion (21) with 1 ≤ m ≤ M is in series connected with a conductor (1, 2, 3, 4, 5, 6) in the (M + 1 - m)^{th} row position of the second primary winding portion (22).
5. The electrical component according to any of the claims 3 or 4 when referring back to claim 3, wherein the secondary winding (30) is a low voltage winding and the primary winding (20) is a high voltage winding.
6. The electrical component according to any of the preceding claims, wherein the first primary winding portion (21) and the second primary winding portion (22) each comprise at least 3, preferably at least 4, conductors (1, 2, 3, 4, 5, 6).
7. The electrical component according to any of the preceding claims, wherein in an operational state of the electrical component, a current of at least 20A, especially at least 100 A, flows through the primary winding (20).
8. The electrical component according to any of the preceding claims, wherein the electrical component comprises a first external electrical connector (41) in series connected with the conductors (1, 2, 3, 4, 5, 6) of the first primary winding portion (21) and a second external electrical connector (42) in series connected with the conductors (1, 2, 3, 4, 5, 6) of the second primary winding portion (22), wherein the first and second primary winding portions (21, 22) are located between the first and second external electrical connector (41, 42).
9. The electrical component according to any of the preceding claims, wherein the first primary winding portion (21) and the second primary winding portion (22) each comprise a cable formed of a group of litz wires and wherein the plurality of parallel connectable conductors (1, 2, 3, 4, 5, 6) are a plurality of parallel connectable litz wires (1, 2, 3, 4, 5, 6).
10. The electrical component according to claim 9, wherein the cable comprises 4 litz wires (1, 2, 3, 4) and wherein the litz wires (1, 2, 3, 4) of the first and second primary winding portions (21, 22) are arranged around the ferromagnetic core (10) in a cross section comprising 2 radial rows and 2 axial rows, wherein an axial direction defines an axial top row and an axial bottom row, whereby a litz wire (1, 2, 3, 4) of a top row of the first primary winding portion (21) is connected in series with a litz wire (1, 2, 3, 4) of a top row of the second primary winding portion (22) and a litz wire (1, 2, 3, 4) of a bottom row of the first primary winding portion (21) is connected in series with a litz wire (1, 2, 3, 4) of a bottom row of the second primary winding portion (22).
11. The electrical component according to claim 9, wherein the litz wires (1, 2, 3, 4, 5, 6) of the first and second primary winding portions (21, 22) are arranged around the ferromagnetic core (10) in a cross section comprising K ≥ 3 axial rows of litz wires (1, 2, 3, 4, 5, 6), each row being arranged at an axial row position, wherein an axial end row position is row position number 1 and an opposite axial end row position is row position number K, wherein each litz wire (1, 2, 3, 4, 5, 6) in the k^{th} row position of the first primary winding portion (21) with 1 ≤ k ≤ K is in series connected with a litz wire (1, 2, 3, 4, 5, 6) in the (K + 1 - k)^{th} row position of the second primary winding portions (22), thereby reducing the sum of the magnetic flux between parallel connectable litz wires (1, 2, 3, 4, 5, 6) of the first primary winding portion (21) and parallel connectable litz wires (1, 2, 3, 4, 5, 6) of the second primary winding portion (22).
12. The electrical component according to claim 11, wherein the cable comprises 6 litz wires (1, 2, 3, 4, 5, 6), wherein the litz wires (1, 2, 3, 4, 5, 6) of the first and second primary winding portions (21, 22) are arranged around the ferromagnetic core (10) in a cross section comprising 2 radial rows and 3 axial rows.
13. The electrical component according to any of claims 1 to 8, wherein the conductors (1, 2, 3, 4, 5, 6) of the first and second primary winding portions (21, 22) are foils.
14. The electrical component according to any of claim 3 and claims 4 to 13 when referring back to claim 3, wherein the first secondary winding portion (31) and the second secondary winding portion (32) are parallel connectable.
15. The electrical component according to any of claim 3 and claims 4 to 13 when referring back to claim 3, wherein the first secondary winding portion (31) and the second secondary winding portion (32) are connected in series.
1. Eine elektrische Komponente, aufweisend:
einen ferromagnetischen Kern (10) mit einem ersten und einem zweiten Schenkel (11, 12);
eine Primärwicklung (20) mit einem ersten Primärwicklungsabschnitt (21), der um den ersten Schenkel (11) des ferromagnetischen Kerns angeordnet ist, und einem zweiten Primärwicklungsabschnitt (22), der um den zweiten Schenkel (12) des ferromagnetischen Kerns angeordnet ist;
wobei der erste Primärwicklungsabschnitt (21) und der zweite Primärwicklungsabschnitt (22) jeweils eine Mehrzahl von Leitern (1, 2, 3, 4, 5, 6) aufweisen, die parallel verbindbar sind und in einem Querschnitt, wobei die Leiter in radialen Reihenpositionen in Bezug aufeinander radial versetzt sind, um den ferromagnetischen Kern angeordnet sind, wobei die Anzahl von Leitern (1, 2, 3, 4, 5, 6) des ersten Primärwicklungsabschnitts (21) gleich der Anzahl von Leitern (1, 2, 3, 4, 5, 6) des zweiten Primärwicklungsabschnitts (22) ist, und jeder der Leiter (1, 2, 3, 4, 5, 6) des ersten Primärwicklungsabschnitts (21) mit einem entsprechenden Leiter (1, 2, 3, 4, 5, 6) des zweiten Primärwicklungsabschnitts (22) in Serie verbunden ist, wodurch ein Leiter (1, 2, 3, 4, 5, 6) einer radial äußeren Reihe des ersten Primärwicklungsabschnitts (21) mit einem Leiter (1, 2, 3, 4, 5, 6) einer radial inneren Reihe des zweiten Primärwicklungsabschnitts (22) in Serie verbunden ist, um dadurch die Summe des Magnetflusses zwischen parallel verbindbaren Leitern (1, 2, 3, 4, 5, 6) des ersten Primärwicklungsabschnitts (21) und parallel verbindbaren Leitern (1, 2, 3, 4, 5, 6) des zweiten Primärwicklungsabschnitts (22) zu reduzieren.
2. Die elektrische Komponente nach Anspruch 1, wobei die elektrische Komponente ein Induktor ist.
3. Die elektrische Komponente nach Anspruch 1, wobei die elektrische Komponente ein Transformator ist, und ferner eine Sekundärwicklung (30) mit einem ersten Sekundärwicklungsabschnitt (31), der um den ersten Schenkel (11) des ferromagnetischen Kerns angeordnet ist, und einem zweiten Sekundärwicklungsabschnitt (32) umfasst, der um den zweiten Schenkel (12) des ferromagnetischen Kerns angeordnet ist.
4. Die elektrische Komponente nach einem der vorhergehenden Ansprüche, wobei der erste und der zweite Primärwicklungsabschnitt (21, 22) in einem Querschnitt, der M Reihen von Leitern (1, 2, 3, 4) umfasst, um den ferromagnetischen Kern angeordnet sind, wobei jede Reihe in einer radialen Reihenposition angeordnet ist, wobei die radial innerste Reihenposition eine Reihenpositionsnummer 1 ist, und die radial äußerste Reihenposition eine Reihenpositionsnummer M ist, wobei jeder Leiter (1, 2, 3, 4) in der m-ten Reihenposition des ersten Primärwicklungsabschnitts (21), wobei 1 ≤ m ≤ M, mit einem Leiter (1, 2, 3, 4, 5, 6) in der (M + 1 - m)-ten Reihenposition des zweiten Primärwicklungsabschnitts (22) in Serie verbunden ist.
5. Die elektrische Komponente nach einem der Ansprüche 3 oder 4 bei Rückverweis auf Anspruch 3, wobei die Sekundärwicklung (30) eine Niederspannungswicklung ist, und die Primärwicklung (20) eine Hochspannungswicklung ist.
6. Die elektrische Komponente nach einem der vorhergehenden Ansprüche, wobei der erste Primärwicklungsabschnitt (21) und der zweite Primärwicklungsabschnitt (22) jeweils mindestens 3, vorzugsweise mindestens 4, Leiter (1, 2, 3, 4, 5, 6) aufweisen.
7. Die elektrische Komponente nach einem der vorhergehenden Ansprüche, wobei in einem Betriebszustand der elektrischen Komponente ein Strom von mindestens 20 A, insbesondere mindestens 100 A, durch die Primärwicklung (20) fließt.
8. Die elektrische Komponente nach einem der vorhergehenden Ansprüche, wobei die elektrische Komponente einen ersten externen elektrischen Verbinder (41), der mit den Leitern (1, 2, 3, 4, 5, 6) des ersten Primärwicklungsabschnitts (21) in Serie verbunden ist, und einen zweiten externen elektrischen Verbinder (42) umfasst, der mit den Leitern (1, 2, 3, 4, 5, 6) des zweiten Primärwicklungsabschnitts (22) in Serie verbunden ist, wobei der erste und der zweite Primärwicklungsabschnitt (21, 22) sich zwischen dem ersten und dem zweiten externen elektrischen Verbinder (41, 42) befinden.
9. Die elektrische Komponente nach einem der vorhergehenden Ansprüche, wobei der erste Primärwicklungsabschnitt (21) und der zweite Primärwicklungsabschnitt (22) jeweils ein Kabel aufweisen, das aus einer Gruppe von Litzen gebildet ist, und wobei es sich bei der Mehrzahl von parallel verbindbaren Leitern (1, 2, 3, 4, 5, 6) um eine Mehrzahl von parallel verbindbaren Litzen (1, 2, 3, 4, 5, 6) handelt.
10. Die elektrische Komponente nach Anspruch 9, wobei das Kabel 4 Litzen (1, 2, 3, 4) umfasst, und wobei die Litzen (1, 2, 3, 4) des ersten und des zweiten Primärwicklungsabschnitts (21, 22) in einem Querschnitt, der 2 radiale Reihen und 2 axiale Reihen umfasst, um den ferromagnetischen Kern (10) angeordnet sind, wobei eine axiale Richtung eine oberste axiale Reihe und eine unterste axiale Reihe definiert, wodurch eine Litze (1, 2, 3, 4) einer obersten Reihe des ersten Primärwicklungsabschnitts (21) mit einer Litze (1, 2, 3, 4) einer obersten Reihe des zweiten Primärwicklungsabschnitts (22) in Serie verbunden ist, und eine Litze (1, 2, 3, 4) einer untersten Reihe des ersten Primärwicklungsabschnitts (21) mit einer Litze (1, 2, 3, 4) einer untersten Reihe des zweiten Primärwicklungsabschnitts (22) in Serie verbunden ist.
11. Die elektrische Komponente nach Anspruch 9, wobei die Litzen (1, 2, 3, 4, 5, 6) des ersten und des zweiten Primärwicklungsabschnitts (21, 22) in einem Querschnitt, der K ≥ 3 axiale Reihen von Litzen (1, 2, 3, 4, 5, 6) umfasst, um den ferromagnetischen Kern (10) angeordnet sind, wobei jede Reihe in einer axialen Reihenposition angeordnet ist, wobei eine axiale Reihen-Endposition eine Reihenpositionsnummer 1 ist und eine gegenüberliegende axiale Reihen-Endposition eine Reihenpositionsnummer K ist, wobei jede Litze (1, 2, 3, 4, 5, 6) in der k-ten Reihenposition des ersten Primärwicklungsabschnitts (21), wobei 1 ≤ k ≤ K, mit einer Litze (1, 2, 3, 4, 5, 6) in der (K + 1 - k) -ten Reihenposition der zweiten Primärwicklungsabschnitten (22) in Serie verbunden ist, um dadurch die Summe des Magnetflusses zwischen parallel verbindbaren Litzen (1, 2, 3, 4, 5, 6) des ersten Primärwicklungsabschnitts (21) und parallel verbindbaren Litzen (1, 2, 3, 4, 5, 6) des zweiten Primärwicklungsabschnitts (22) zu reduzieren.
12. Die elektrische Komponente nach Anspruch 11, wobei das Kabel 6 Litzen (1, 2, 3, 4, 5, 6) umfasst, wobei die Litzen (1, 2, 3, 4, 5, 6) des ersten und des zweiten Primärwicklungsabschnitts (21, 22) in einem Querschnitt, der 2 radiale Reihen und 3 axiale Reihen umfasst, um dem ferromagnetischen Kern (10) angeordnet sind.
13. Die elektrische Komponente nach einem der Ansprüche 1 bis 8, wobei die Leiter (1, 2, 3, 4, 5, 6) des ersten und des zweiten Primärwicklungsabschnitts (21, 22) Folien sind.
14. Die elektrische Komponente nach einem der Ansprüche 3 und 4 bis 13 bei Rückverweis auf Anspruch 3, wobei der erste Sekundärwicklungsabschnitt (31) und der zweite Sekundärwicklungsabschnitt (32) parallel verbindbar sind.
15. Die elektrische Komponente nach einem der Ansprüche 3 und 4 bis 13 bei Rückverweis auf Anspruch 3, wobei der erste Sekundärwicklungsabschnitt (31) und der zweite Sekundärwicklungsabschnitt (32) in Serie verbunden sind.
1. Un composant électrique, comprenant :
un noyau ferromagnétique (10) pourvu d'une première et d'une deuxième branche (11, 12) ;
un enroulement primaire (20) pourvu d'un premier tronçon d'enroulement primaire (21) agencé autour de la première branche (11) du noyau ferromagnétique et d'un deuxième tronçon d'enroulement primaire (22) agencé autour de la deuxième branche (12) du noyau ferromagnétique ;
le premier tronçon d'enroulement primaire (21) et le deuxième tronçon d'enroulement primaire (22) comprenant chacun une pluralité de conducteurs (1, 2, 3, 4, 5, 6) susceptibles d'être reliés en parallèle et agencés autour du noyau ferromagnétique selon une coupe transversale où les conducteurs sont décalés radialement entre eux à des positions de rangées radiales, le nombre de conducteurs (1, 2, 3, 4, 5, 6) du premier tronçon d'enroulement primaire (21) étant égal au nombre de conducteurs (1, 2, 3, 4, 5, 6) du deuxième tronçon d'enroulement primaire (22) et chacun des conducteurs (1, 2, 3, 4, 5, 6) du premier tronçon d'enroulement primaire (21) étant relié en série avec un conducteur (1, 2, 3, 4, 5, 6) correspondant du deuxième tronçon d'enroulement primaire (22), moyennant quoi un conducteur (1, 2, 3, 4, 5, 6) d'une rangée radialement extérieure du premier tronçon d'enroulement primaire (21) est relié en série avec un conducteur (1, 2, 3, 4, 5, 6) d'une rangée radialement intérieure du deuxième tronçon d'enroulement primaire (22), pour ainsi réduire la somme du flux magnétique entre des conducteurs (1, 2, 3, 4, 5, 6) susceptibles d'être reliés en parallèle du premier tronçon d'enroulement primaire (21) et des conducteurs (1, 2, 3, 4, 5, 6) susceptibles d'être reliés en parallèle du deuxième tronçon d'enroulement primaire (22).
2. Le composant électrique selon la revendication 1, lequel composant électrique est une bobine d'inductance.
3. Le composant électrique selon la revendication 1, lequel composant électrique est un transformateur et comprend en outre un enroulement secondaire (30) pourvu d'un premier tronçon d'enroulement secondaire (31) agencé autour de la première branche (11) du noyau ferromagnétique et d'un deuxième tronçon d'enroulement secondaire (32) agencé autour de la deuxième branche (12) du noyau ferromagnétique.
4. Le composant électrique selon l'une quelconque des revendications précédentes, dans lequel les premier et deuxième tronçons d'enroulement primaire (21, 22) sont agencés autour du noyau ferromagnétique selon une coupe transversale comprenant M rangées de conducteurs (1, 2, 3, 4), chaque rangée étant agencée à une position de rangée radiale, la position de rangée radialement la plus intérieure étant la position de rangée numéro 1 et la position de rangée radialement la plus extérieure étant la position de rangée numéro M, chaque conducteur (1, 2, 3, 4) dans la m-ième position de rangée du premier tronçon d'enroulement primaire (21), 1 ≤ m ≤ M, étant relié en série avec un conducteur (1, 2, 3, 4, 5, 6) dans la (M + 1 - m)-ième position de rangée du deuxième tronçon d'enroulement primaire (22).
5. Le composant électrique selon l'une quelconque des revendications 3 ou 4 lorsqu'elle se réfère à la revendication 3, dans lequel l'enroulement secondaire (30) est un enroulement basse tension et l'enroulement primaire (20) est un enroulement haute tension.
6. Le composant électrique selon l'une quelconque des revendications précédentes, dans lequel le premier tronçon d'enroulement primaire (21) et le deuxième tronçon d'enroulement primaire (22) comprennent chacun au moins 3, de préférence au moins 4, conducteurs (1, 2, 3, 4, 5, 6) .
7. Le composant électrique selon l'une quelconque des revendications précédentes, dans lequel, dans un état de fonctionnement du composant électrique, un courant d'au moins 20 A, plus particulièrement d'au moins 100 A, circule dans l'enroulement primaire (20).
8. Le composant électrique selon l'une quelconque des revendications précédentes, lequel composant électrique comprend un premier connecteur électrique externe (41) relié en série avec les conducteurs (1, 2, 3, 4, 5, 6) du premier tronçon d'enroulement primaire (21) et un deuxième connecteur électrique externe (42) relié en série avec les conducteurs (1, 2, 3, 4, 5, 6) du deuxième tronçon d'enroulement primaire (22), les premier et deuxième tronçons d'enroulement primaire (21, 22) étant situés entre les premier et deuxième connecteurs électriques externes (41, 42).
9. Le composant électrique selon l'une quelconque des revendications précédentes, dans lequel le premier tronçon d'enroulement primaire (21) et le deuxième tronçon d'enroulement primaire (22) comprennent chacun un câble formé d'un groupe de fils de Litz, et dans lequel la pluralité de conducteurs (1, 2, 3, 4, 5, 6) susceptibles d'être reliés en parallèle sont une pluralité de fils de Litz (1, 2, 3, 4, 5, 6) susceptibles d'être reliés en parallèle.
10. Le composant électrique selon la revendication 9, dans lequel le câble comprend 4 fils de Litz (1, 2, 3, 4) et dans lequel les fils de Litz (1, 2, 3, 4) des premier et deuxième tronçons d'enroulement primaire (21, 22) sont agencés autour du noyau ferromagnétique (10) selon une coupe transversale comprenant 2 rangées radiales et 2 rangées axiales, une direction axiale définissant une rangée axiale supérieure et une rangée axiale inférieure, moyennant quoi un fil de Litz (1, 2, 3, 4) d'une rangée supérieure du premier tronçon d'enroulement primaire (21) est reliée en série avec un fil de Litz (1, 2, 3, 4) d'une rangée supérieure du deuxième tronçon d'enroulement primaire (22) et un fil de Litz (1, 2, 3, 4) d'une rangée inférieure du premier tronçon d'enroulement primaire (21) est reliée en série avec un fil de Litz (1, 2, 3, 4) d'une rangée inférieure du deuxième tronçon d'enroulement primaire (22).
11. Le composant électrique selon la revendication 9, dans lequel les fils de Litz (1, 2, 3, 4, 5, 6) des premier et deuxième tronçons d'enroulement primaire (21, 22) sont agencés autour du noyau ferromagnétique (10) selon une coupe transversale comprenant K ≥ 3 rangées axiales de fils de Litz (1, 2, 3, 4, 5, 6), chaque rangée étant agencée à une position de rangée axiale, une position de rangée d'extrémité axiale étant la position de rangée numéro 1 et une position de rangée d'extrémité axiale opposée étant la position de rangée numéro K, chaque fil de Litz (1, 2, 3, 4, 5, 6) dans la k-ième position de rangée du premier tronçon d'enroulement primaire (21), 1 ≤ k ≤ K, étant relié en série avec un fil de Litz (1, 2, 3, 4, 5, 6) dans la (K + 1 - k)-ième position de rangée des deuxièmes tronçons d'enroulement primaire (22), pour ainsi réduire la somme du flux magnétique entre des fils de Litz (1, 2, 3, 4, 5, 6) susceptibles d'être reliés en parallèle du premier tronçon d'enroulement primaire (21) et des fils de Litz (1, 2, 3, 4, 5, 6) susceptibles d'être reliés en parallèle du deuxième tronçon d'enroulement primaire (22).
12. Le composant électrique selon la revendication 11, dans lequel le câble comprend 6 fils de Litz (1, 2, 3, 4, 5, 6), les fils de Litz (1, 2, 3, 4, 5, 6) des premier et deuxième tronçons d'enroulement primaire (21, 22) étant agencés autour du noyau ferromagnétique (10) selon une coupe transversale comprenant 2 rangées radiales et 3 rangées axiales.
13. Le composant électrique selon l'une quelconque des revendications 1 à 8, dans lequel les conducteurs (1, 2, 3, 4, 5, 6) des premier et deuxième tronçons d'enroulement primaire (21, 22) sont des feuilles.
14. Le composant électrique selon l'une quelconque parmi la revendication 3 et les revendications 4 à 13 lorsqu'elles se réfèrent à la revendication 3, dans lequel le premier tronçon d'enroulement secondaire (31) et le deuxième tronçon d'enroulement secondaire (32) sont susceptibles d'être reliés en parallèle.
15. Le composant électrique selon l'une quelconque parmi la revendication 3 et les revendications 4 à 13 lorsqu'elles se réfèrent à la revendication 3, dans lequel le premier tronçon d'enroulement secondaire (31) et le deuxième tronçon d'enroulement secondaire (32) sont reliés en série.