ATBECHDEDKESFRGBGRITLILUNLSEMCPTIESILTLVFIROMKCYALTRBGCZEEHUPLSKBAHRIS..MTNORSMESMMAKHTNMD..........
J
BDM Ver 2.0.24 - 1100000/0
4362054
EUROPEAN PATENT APPLICATION
A1
20240501
EP
22203642.8
20221025
en
en
en
20240501
202418
20240501
202418
H01H 33/70 20060101AFI20230330BHEP
H01H 33/7038 20130101 FI20230322BHEP
de
VERFAHREN ZUM ERMITTELN EINES STEUERSIGNALS EINES ELEKTROMAGNETISCHEN ANTRIEBS EINER UNTERBRECHEREINHEIT UND UNTERBRECHEREINHEIT FÜR EINE GASISOLIERTE HOCH- ODER MITTELSPANNUNGSEINRICHTUNG
en
METHOD FOR DETERMINING A CONTROL SIGNAL OF AN ELECTROMAGNETIC DRIVE OF AN INTERRUPTER UNIT, AND INTERRUPTER UNIT FOR A GAS-INSULATED HIGH OR MEDIUM VOLTAGE DEVICE
fr
PROCÉDÉ DE DÉTERMINATION D'UN SIGNAL DE COMMANDE D'UN ENTRAÎNEMENT ÉLECTROMAGNÉTIQUE D'UNE UNITÉ D'INTERRUPTEUR ET UNITÉ D'INTERRUPTEUR POUR UN DISPOSITIF À HAUTE OU MOYENNE TENSION ISOLÉ AU GAZ
1
Hitachi Energy Ltd
102015137
HD 41621/GQ
Brown-Boveri-Strasse 5
8050 Zürich
CH
GALLETTI, Bernardo
5415 Nussbaumen
CH
LU, Peng
Tianjin, 300300
CN
SEEGER, Martin
5745 Safenwil
CH
KOTILAINEN, Sami
5443 Niederrohrdorf
CH
RADISAVLJEVIC, Branimir
8037 Zurich
CH
Michalski Hüttermann & Partner Patentanwälte mbB
101375650
Kaistraße 16A
40221 Düsseldorf
DE
AL
AT
BE
BG
CH
CY
CZ
DE
DK
EE
ES
FI
FR
GB
GR
HR
HU
IE
IS
IT
LI
LT
LU
LV
MC
ME
MK
MT
NL
NO
PL
PT
RO
RS
SE
SI
SK
SM
TR
BA
KH
MA
MD
TN
The invention relates to a computer implemented method for determining a control signal of an electromagnetic drive (20) of an interrupter unit (10) for a high or medium voltage device, wherein the interrupter unit (10) comprises a first arcing contact (12) and a second arcing contact (14), wherein the interrupter unit (10) comprises at least one electromagnetic drive (20) for driving an axial motion of the first and/or second arcing contact (12,14) from a closed position to an open position based on the control signal, comprising the step of
determining the control signal of the electromagnetic drive (20) such that in a second timeframe (52) that occurs during opening operation and before the final distance between the first and second arcing contact (12,14) is reached, a distance (18) between the first and the second arcing contact (12,14) is kept constant ± 20 %.
Furthermore, the invention relates to an interrupter unit (10) comprising a control unit (22) configured to perform the above method.
Furthermore, the invention relates to a high or medium voltage device comprising the above interrupter unit (10).

Technical Field
The invention relates to a computer implemented method for determining a control signal of an electromagnetic drive of an interrupter unit for a high or medium voltage device.
The present invention also relates to a control unit for determining a control signal of an electromagnetic drive for an interrupter unit of a high or medium voltage device, wherein the control unit is configured to perform the above method.
The present invention further relates to an interrupter unit for a gas-insulated high or medium voltage device comprising the above control unit.
Furthermore, the present invention relates to a gas-insulated high or medium voltage device comprising the above interrupter unit.

Background Art
High or medium voltage devices, such as circuit breakers and switchgears are essential for the protection of technical equipment, especially in the high voltage range. For example, circuit breakers are predominantly used for interrupting a current, when an electrical fault occurs. As an example, circuit breakers have the task of opening arcing contacts, quench an arc, and keeping the arcing contacts apart from one another in order to avoid a current flow even in case of high electrical potential originating from the electrical fault itself. Circuit breakers may break medium to high short circuit currents of typically 1 kA to 80 kA at medium to high voltages of 12 kV to 72 kV and up to 1200 kV. Thus, high or medium voltage devices accommodate high-voltage conductors such as conductors to which a high voltage is applied.
Some high or medium voltage devices, namely gas-insulated high or medium voltage devices comprise an insulation gas, for example SF_6, in order to shield and insulate the high-voltage conductor from other component and/or to improve quenching of an arc, when operating arcing contacts. In particular the insulation gas is used for extinguishing the arc generated in an arcing region between the arcing contacts when a current is interrupted and is thus also called arc extinguishing gas.
An electric arc is made up by a flux of electrons and a flux of ions which circulate in opposite directions between the arcing contacts. When the temperature of the arc decreases, ions and electrons recombine and the arc extinguishing gas resumes its isolating properties. In a gas insulated circuit breaker, a gaseous mantle surrounds a core of the arc. The temperature of the gaseous mantle decreases as the distance from the arc axis is increased. The current flow is interrupted when an efficient blast of arc extinguishing gas is applied to cool the arc and extinguish it. The capability of how efficient the arc is extinguished at the zero crossing of the alternating fault current by a high or medium voltage device is called thermal interruption performance.
The post-arc phase has a critical role in the current interruption process, since during this phase the dielectric strength of the arc extinguishing gas has to be recovered. The hot gas generated from the arc discharge in the interruption process depletes the dielectric recovery strength between the arcing contacts and can potentially lead to re-ignition of the arc after current-zero when the transient recovery voltage rises between the arcing contacts. In other words, even though the thermal interruption has been successfully accomplished, a dielectric breakdown might occur leading to re-ignition and causing the fault-current to flow to the load again. The capability of how efficient re-ignition is prevented by a high or medium voltage device is called dielectric recovery performance.
A performance problem of gas-insulated high or medium voltage devices is that the thermal interruption performance and the dielectric recovery performance of the gas-insulated high or medium voltage device varies for different interruption duties of the high or medium voltage device.

Summary of invention
It is an object of the invention to provide means to improve the interruption performance of a gas-insulated high or medium voltage device and in particular to improve the thermal interruption performance and/or the dielectric recovery performance of the gas-insulated high or medium voltage device.
The object of the invention is solved by the features of the independent claims. Modified embodiments are detailed in the dependent claims.
Thus, the object is solved by a computer implemented method for determining a control signal of an electromagnetic drive of an interrupter unit for a high or medium voltage device, wherein the interrupter unit comprises a first arcing contact and a second arcing contact, wherein for an opening operation of the interrupter unit at least one of the arcing contacts is axially movable along a switching axis thereby bringing the first arcing contact and second arcing contact from a closed position with direct contact between the first and second arcing contacts into an open position with a final distance between the first and second arcing contacts, wherein the interrupter unit comprises at least one electromagnetic drive for driving the axial motion of the first and/or second arcing contact from the closed position to the open position based on the control signal, comprising the step of
- determining the control signal of the electromagnetic drive such that in a second timeframe that occurs during opening operation and before the final distance between the first and second arcing contact is reached, a distance between the first and the second arcing contact is kept constant ± 20 %.
Furthermore, the object is solved by a control unit for determining a control signal of an electromagnetic drive of an interrupter unit for a high or medium voltage device, wherein the control unit is configured to perform the above method.
The object is also solved by an interrupter unit for a gas-insulated high or medium voltage device comprising a first arcing contact and a second arcing contact, wherein for an opening operation of the interrupter unit at least one of the arcing contacts is axially movable along a switching axis thereby bringing the first arcing contact and second arcing contact from a closed position with direct contact between the first and second arcing contact into an open position with a final distance between the first and second arcing contact, wherein the interrupter unit comprises at least one electromagnetic drive for driving the axial motion of the first and/or second arcing contact from the closed position to the open position based on a control signal, and wherein the interrupter unit comprises the above control unit.
Furthermore, the object is also solved by a gas-insulated high or medium voltage device comprising the above interrupter unit, and wherein the high or medium voltage device comprises an arc extinguishing gas.
One aspect of the invention is, that the motion of the first and/or second arcing contact from the closed position to the open position is in a certain timeframe - which is called second timeframe and occurs during the opening operation - such that the distance between the arcing contacts is essentially constant. It has been observed that the dielectric recovery performance and the thermal interruption performance of high or medium voltage devices are dependent on a duration of a timeframe during which the arc is burning - also called arcing time. It was found that a motion of the arcing contacts by which the distance between the arcing contact is essentially kept constant in the second timeframe improves dielectric recovery performance and thermal interruption performance of the high or medium voltage device.
In order to provide the axial motion, the interrupter unit comprises at least one electromagnetic drive for driving the axial motion of the first and/or second arcing contact from the closed position to the open position based on the control signal, and further comprises the control unit that is configured to perform the method for determining the control signal. The electromagnetic drive is preferably configured such that a stroke of the electromagnetic drive is controlled by the control signal. In other words, the electromagnetic drive is a programmable electromagnetic drive providing a stroke characteristic based on the control signal. Further preferably the control signal is a digital signal that can be processed by the control unit.
In other words, the axial motion of the first and/or second arcing contact from the closed to the open position preferably comprises a second timeframe in which the distance between the first and the second arcing contact is essentially kept constant. Being essentially kept constant means that the distance between the first arcing contact and the second arcing contact does only vary for ± 20 % of a predefined distance in the second timeframe.
It was observed that the interruption performance of the high or medium voltage device depends on the relative position of the first or second arcing contact with respect to an insulating nozzle. At the zero crossing of the alternating short circuit current, also called current-zero - which is the timepoint when the arc is extinguished - one of the arcing contacts is typically located somewhere in a diverging region of the insulating nozzle. It was found that the arc extinguishing gas conditions in the region in front of this arcing contact generally gets worse for current interruption when the position of the arcing contact moves farther into the diverging region of the insulating nozzle. Hence, by keeping the distance between the first and second arcing contacts essentially constant in the second timeframe, the arcing contact is hindered to move farther into the diverging region. Thus, also for long arcing times good interruption conditions are provided.
Furthermore, the control signal of the electromagnetic drive is determined such that the distance between the first and second arcing contacts in the second timeframe does not correspond to the final distance. In other words, the distance between the first and second arcing contact in the second timeframe is not the final distance, but a distance shorter than the final distance. This preferably also means that the second timeframe is not at the end of the opening operation. Further preferably the final distance between the arcing contacts corresponds to a distance between the first and second arcing contacts that is required by the open gap withstand insulation requirement of the interrupter unit.
According to a preferred embodiment of the invention the step of determining the control signal of the electromagnetic drive comprises determining the control signal such that in a first timeframe of the opening operation, wherein the first timeframe immediately precedes the second timeframe, the distance between the first and second arcing contacts increases, and in a third timeframe of the opening operation, wherein the third timeframe immediately follows the second timeframe, the distance between the first arcing contact and the second arcing contact increases until the final distance between the first arcing contact and the second arcing contact is achieved. In other words, it is preferred if the opening operation comprises three consecutive timeframes, wherein in the first timeframe the distance between the first and second arcing contact increases, and preferably continuously increases, in the second timeframe the distance is essentially kept constant, and in the third timeframe the distance again increases, and preferably continuously increases, until the final distance is achieved.
According to another preferred embodiment of the invention the step of determining the control signal of the electromagnetic drive comprises determining the control signal of the electromagnetic drive, such that in the second timeframe of the opening operation the first arcing contact and the second arcing contact have no motion, or such that in the second timeframe of the opening operation the motion of the first arcing contact is essentially matched to the motion of the second arcing contact. Having no motion means in the context of this application that the first and the second arcing contact have no absolute motion.
In other words, the essentially constant distance between the first and second arcing contacts in the second timeframe can be achieved by two variants:
In the first variant neither the first nor the second arcing contact have an absolute motion during the second timeframe. This is particular preferred for interrupter units where only one arcing contact is axially movable and the other arcing contact is stationary. Circuit breakers having such interrupter units are called single-motion circuit breakers. Furthermore, the first variant is also preferred for interrupter units, where the electromagnetic drive drives the axial motion of the first or second arcing contact and the motion is transferred to the other arcing contact by a gear linkage mechanism.
In the second variant, the motion of one of the arcing contacts is essentially matched to the motion of the other arcing contact in the second timeframe, such that the distance between the arcing contacts is kept constant ± 20 %. As in the first timeframe and in the third timeframe - i.e. the timeframes that precede and follow the second timeframe - the distance between the arcing contact preferably increases, this also preferably means for interrupter units where both arcing contacts perform a motion during opening operation, that in this variant the motion of the first or the second arcing contact preferably comprises an inversion of the motion direction.
In order to improve the interruption capabilities of the interrupter unit it is beneficial to get cooler and denser arc extinguishing gas in the region around the arcing contact that is located somewhere in a diverging region of the insulating nozzle at current-zero. In relation to this and according to another preferred embodiment of the invention, the interrupter unit comprises an insulating nozzle, wherein the insulating nozzle comprises a throat region and adjacent to the throat region a diverging region, wherein the throat region forms a cylindrically shaped throat channel and the diverging region forms a diverging channel, wherein during opening operation a tip of one arcing contact first moves through the cylindrically shaped throat channel and afterwards through the diverging channel, and wherein the step of determining the control signal of the electromagnetic drive comprises determining the control signal such that the second timeframe starts when the distance between the first and second arcing contacts is such that an insulating nozzle outflow limiting area defined by the minimum cross-section area between the diverging channel and the tip of the one arcing contact lying within the diverging channel is essentially equal to a minimum cross-section area of the cylindrically shaped throat channel. Being essentially equal preferably means that the outflow limiting area in the insulating nozzle divergent is equal to or exceeds the minimum cross-section area of the cylindrically shaped throat channel, and preferably exceeds the minimum cross-section area of the throat channel by maximally 30 %.
Preferably, the one arcing contact that moves through the cylindrically shaped throat channel and the diverging channel during opening operation is the plug contact. In other words, the position of the first and second arcing contacts with respect to each other, at which the second timeframe starts, is preferably a position where the arc extinguishing gas has beneficial flow conditions, and more preferably where the annular shaped cross-section area defined by the contours of the tip of the plug contact and the contours of the diverging channel of the insulating nozzle equals or exceeds, and preferably exceeds by maximally 30 %, the circular shaped cross-section area defined by the contours of the cylindrically shaped throat channel of the throat region. These conditions typically define the minimum arcing time of the interrupter unit. Hence, and according to another preferred embodiment of the invention, the step of determining the control signal of the electromagnetic drive comprises determining the control signal such that the second timeframe starts at the minimum arcing time of the interrupter unit.
According to another preferred embodiment of the invention, the step of determining the control signal of the electromagnetic drive comprises determining the control signal such that the second timeframe lasts until arc extinction of a longest arcing time of the interrupter unit. Preferably as arc extinction happens at current-zero, the arc extinction of the longest arcing time of the interrupter unit is defined by the minimum arcing time of the interrupter unit and the frequency of the alternating fault current. Further preferably the distance between the first and second arcing contacts in the third timeframe increased rapidly to attain the final distance required by open gap insulation tests, such as lightning impulse, and/or dielectric integrity.
Further preferably, the method comprises the step of receiving a fault current signal, and wherein the step of determining the control signal of the electromagnetic drive comprises determining the control signal of the electromagnetic drive taking the received fault current signal and the type of interrupter unit into account, such that
- in cases where the interrupter unit is a puffer-type interrupter unit and the fault current signal is a capacitive current switching or a short-line fault duty, the distance between the first and the second arcing contacts in the second timeframe is essentially kept constant, and/or
- in cases where the interrupter unit is a self-blast interrupter unit and the fault current signal is a low current duty, the distance between the first and the second arcing contacts in the second timeframe is essentially kept constant, and/or
- in cases where the interrupter unit is a self-blast interrupter unit and the fault current signal is a high current duty, the distance between the first and the second arcing contacts in the second timeframe is essentially kept constant or increases.
Further preferably the fault current signal is a digital signal that can be processed by the control unit. It was found that keeping the distance between the first and second arcing contact in the second timeframe essentially constant increases the performance of puffer-type interrupter unit for, for example, capacitive current switching and for short-line fault duties. Furthermore, also the dielectric recovery performance of self-blast interrupter units for low current duties can be significantly increased by keeping the distance between the first and second arcing contact essentially constant in the second timeframe. Furthermore, in cases where the interrupter unit is a self-blast interrupter unit and the fault current signal is a high current duty, it was found that keeping the distance between the first and second arcing contact in the second timeframe essentially constant does not negatively affect the interruption performance with respect to a movement of the arcing contacts, where the distance in the second timeframe increases.
Other aspects and advantages of the method for determining the control signal of the electromagnetic drive of the interrupter unit for a high or medium voltage device are directly and unambiguously derived by the person skilled in the art from the description of the interrupter unit, the description of the gas-insulated high or medium voltage device and the figure description.
As already mentioned, the invention is also directed to the control unit configured to perform the above described method and also to the interrupter unit for a gas-insulated high or medium voltage device comprising the first arcing contact and the second arcing contact, wherein for the opening operation of the interrupter unit at least one of the arcing contacts is axially movable along a switching axis thereby bringing the first arcing contact and second arcing contact from the closed position with direct contact between the first and second arcing contacts into the open position with a final distance between the first and second arcing contacts, wherein the interrupter unit comprises the at least one electromagnetic drive for driving the axial motion of the first and/or second arcing contact from the closed position to the open position based on the control signal, and wherein the interrupter unit comprises the control unit.
As the motion of the arcing contact of the interrupter unit are such that in the second timeframe that occurs during opening operation and before the final distance between the first and second arcing contact is reached, the distance between the first and the second arcing contact is essentially kept constant, beneficial arc extinguishing gas conditions can be achieved during the opening operation and thus the performance of the interrupter unit is enhanced.
According to a preferred embodiment of the invention the interrupter unit comprises a sensing device communicationally connected to the control unit, and wherein the sensing device is configured to generate a fault current signal based on analysis of a fault current and to send the fault current signal to the control unit. This is an easy way to ensure that the motion of the first and/or second arcing contact is adapted to the fault current signal. In other words, the control unit is preferably coupled to the sensing devices in order to produce a control signal for a motion of the first and/or second arcing contact that is adapted to different duties of the interrupter unit. By customizing the travel curves of the first and/or second arcing contact, the electromagnetic drive provides the specific stroke characteristics, allowing an optimal interruption performance for diverse interruption duties. Furthermore, the sensing device preferably performs an analysis of the fault current and, based on it, will send the fault current signal to the control unit, which than proposes the motion law for the interruption duties for which it is beneficial.
According to another preferred embodiment of the invention, the interrupter unit is configured such that for the opening operation only the first or second arcing contact is axially movable along the switching axis, wherein the electromagnetic drive drives the axial motion of the axially movable arcing contact based on the control signal, and wherein the control unit is configured to determine the control signal, such that in the second timeframe of the opening operation the first arcing contact and the second arcing contact have no motion. In other words, in this embodiment the interrupter unit is configured as a single motion interruption unit, where one arcing contact is stationary during the opening operation. In this case in the second timeframe of the opening operation the first arcing contact and the second arcing contact have no absolute motion.
According to an alternative embodiment of the invention, the interrupter unit is configured such that for the opening operation of the interrupter unit the first and second arcing contacts are axially movable along the switching axis, wherein the electromagnetic drive is connected to the first or second arcing contact and drives the axial motion of said driving arcing contact based on the control signal, wherein the interrupter unit comprises a gear linkage mechanism connecting the motion of said driving arcing contact to the motion of the other indirectly driven arcing contact, and wherein the control unit is configured to determine the control signal, such that in the second timeframe of the opening operation the first arcing contact and the second arcing contact have no motion. In other words, in this embodiment one of the arcing contacts, i.e. the driving arcing contact, is directly connected to the electromagnetic drive, while the other arcing contact, i.e. the driven arcing contact, is indirectly driven via a gear linkage mechanism by the driving arcing contact.
According to a further alternative embodiment of the invention the interrupter unit is free of a gear linkage mechanism connecting the motion of one of the arcing contacts to the motion of the other arcing contact, wherein the electromagnetic drive drives the axial motion of the first and/or second arcing contact based on the control signal, and wherein the control unit is configured to determine the control signal, such that in the second timeframe of the opening operation the motion of the first arcing contact is essentially matched to the motion of the second arcing contact. In this preferred embodiment the interrupter unit is free of a gear linkage mechanism, which makes the structure of the interrupter unit less complex. Furthermore, the control signal can be a control signal dedicated for the motion of only one of the arcing contacts or it can be a control signal dedicated for the motion of both arcing contacts.
According to another alternative and particular preferred embodiment of the invention the interrupter unit is configured such that for the opening operation of the interrupter unit the first and second arcing contacts are axially movable along the switching axis, wherein the electromagnetic drive is connected to the first or second arcing contact and drives the axial motion of said arcing contact based on the control signal, wherein the interrupter unit is free of a gear linkage mechanism connecting the motion of said arcing contact to the motion of the other arcing contact, and wherein the control unit is configured to determine the control signal, such that in the second timeframe of the opening operation the motion of said arcing contact is essentially matched to the motion of the other arcing contact. In this embodiment the motion of the arcing contact not driven by the electromagnetic drive is preferably driven by a conventional drive such as a spring drive or a hydraulic drive. In particular the conventional drive preferably provides a physically predetermined stroke characteristic and is not programmable.
In connection to the above and according to another preferred embodiment of the invention the interrupter unit is configured such that for the opening operation of the interrupter unit the first and second arcing contacts are axially movable along the switching axis, wherein the interrupter unit is free of a gear linkage mechanism connecting the motion of one of the arcing contacts to the motion of the other arcing contact, wherein the electromagnetic drive drives the axial motion of the first arcing contact based on the control signal, wherein the interrupter unit comprises a drive for driving the motion of the second arcing contact, wherein the motion of the second arcing contact effects a pressurization of a pressurization chamber, and wherein the control unit is configured to determine the control signal, such that in the second timeframe of the opening operation the motion of the first arcing contact is essentially matched to the motion of the second arcing contact. The drive that effects the motion of the second arcing contact and the pressurization of the pressurization chamber is preferably not a programmable drive, but a driven that provides a physically predetermined stroke characteristic such as a spring drive or a hydraulic drive.
According to another preferred embodiment of the invention the interrupter unit is configured such that for the opening operation of the interrupter unit the first and second arcing contacts are axially movable along the switching axis, wherein the interrupter unit comprises two electromagnetic drives, each connected to one of the arcing contacts for driving the axial motion of the arcing contacts based on the control signal, wherein the interrupter unit is free of a gear linkage mechanism connecting the motion of one of the arcing contacts to the motion of the other arcing contact, and wherein the control unit is configured to determine the control signal, such that in the second timeframe of the opening operation the first arcing contact and the second arcing contact have no motion, or such that in the second timeframe of the opening operation the motion of one arcing contact is essentially matched to the motion of the other arcing contact. In this particular embodiment the control signal is a signal dedicated for two electromagnetic drives.
As already mentioned, the invention also relates to a gas-insulated high or medium voltage device comprising the above-described interrupter unit, and wherein the high or medium voltage device comprises the arc extinguishing gas.
Preferably the arc extinguishing gas is selected from CO_2, SF_6, mixtures of CO_2 or SF_6 with a carrier gas and/or mixtures of fluoroketons and/or fluoronitriles with a carrier gas. The carrier gas for use with fluoroketons and/or fluoronitriles and/or SF_6 may comprise air, N_2, CO_2, and mixtures thereof. Further preferably the arc extinguishing gas may have a reduced fluorine content compared to SF_6, or may even be essentially fluorine free.
According to another preferred embodiment of the invention the gas-insulated high or medium voltage device is preferably a circuit breaker and more preferably the gas-insulated high or medium voltage device is configured as a puffer-type circuit breaker or a self-blast circuit breaker. Furthermore, in the context of this invention medium to high voltages means voltages of 12 kV to 72 kV (medium voltage) and up to 1200 kV (high voltage).
These and other aspects of the invention will be apparent from and elucidated with reference to the embodiments described hereinafter.
In the drawings:
Fig. 1
schematically shows an interrupter unit of a high or medium voltage device according to a preferred embodiment of the invention,
Fig. 2
schematically shows the interrupter unit of figure 1, when a final distance between a first and second arcing contact is reached,
Fig. 3
schematically shows in a) b) and c) each a diagram describing the relative position of a first and second arcing contact, and the corresponding distance between the first and second arcing contact during an opening operation of the interrupter unit of figure 1,
Fig. 4
schematically shows a diagram describing the relative position of a first and second arcing contact, and the corresponding distance between the first and second arcing contact during an opening operation according to a further embodiment of the invention,
Fig. 5
schematically shows in the upper half flow streamlines for a low current duty at current zero for the opening operation shown in figure 3 for the interrupter unit of figures 1 and 2, and in the lower half flow streamlines for a low current duty at current zero for an opening operation of an interrupter unit according to prior art.

Description of embodiments
Fig. 1 schematically shows an interrupter unit 10 for a gas-insulated high or medium voltage device, according to a preferred embodiment. The interrupter unit 10 comprises a first arcing contact 12 and a second arcing contact 14. In this embodiment the first arcing contact 12 has the form of a plug contact 12 and the second arcing contact 14 is configured as tulip contact 14. The plug contact 12 is axially movable along a switching axis 16. The tulip contact 14 is also axially movable along the switching axis 16 and is further configured to engage around a proximal portion of the plug contact 12, in the closed position of the contacts 12, 14 (not shown in figure 1). During opening operation of the interrupter unit 10, a distance 18 between the plug contact 12 and tulip contact 14 increases until a final distance 18 is reached.
Figure 1 shows the interrupter unit 10 during the opening operation, while figure 2 shows the interrupter unit 10 when the final distance 18 between the first and second arcing contacts 12,14 is reached.
The interrupter unit 10 further comprises an electromagnetic drive 20 (only schematically shown) for driving the axial motion of the first arcing contact 12, i.e. the plug contact, along the switching axis 16 based on a control signal and further comprises a control unit 22 for determining the control signal. The control unit 22 is communicationally connected to the electromagnetic drive 20 and configured to send the control signal to the electromagnetic drive 20. In this embodiment the interrupter unit 10 further comprises a sensing device 24 communicationally connected to the control unit 22, wherein the sensing device 24 is configured to generate a fault current signal based on analysis of a fault current and to send the fault current signal to the control unit 22.
Furthermore, in this embodiment the interrupter unit 10 is free of a gear linkage mechanism connecting the motion of the first arcing contact 12 to the motion of the second arcing contact 14. Instead, the motion of the second arcing contact 14 is affected by another drive (not shown in figure 1), in this embodiment a spring drive.
As can also be seen in figure 1, the interrupter unit 10 comprises a nozzle system 26 wherein the nozzle system 26 at least partially encloses the second contact 14. The nozzle system 26 comprises a heating channel 28 for guiding an arc extinguishing gas in a flow-guiding direction 30 from a pressurization chamber to an arcing region 32 for extinguishing an arc formed in the arcing region 32 between the first arcing contact 12 and the second arcing contact 14 during the opening operation of the arcing contacts 12,14.
In this embodiment the nozzle system 26 comprises an auxiliary nozzle 34 and an insulating nozzle 36 arranged around the auxiliary nozzle 34 and the heating channel 28 is formed in between the insulating nozzle 36 and the auxiliary nozzle 34.
The insulating nozzle 36 comprises a throat region 38 and adjacent to the throat region 38 a diverging region 40, wherein the throat region 38 forms a cylindrically shaped throat channel and the diverging region 40 forms a diverging channel. During opening operation, a tip 42 of the plug contact 12 first moves through the cylindrically shaped throat channel and afterwards through the diverging channel until the final distance 18 between the two arcing contacts 12, 14 is reached.
As already mentioned, the interrupter unit 10 comprises the control unit 22 for determining the control signal. For this the control unit 22 is configured to perform a method for determining the control signal. In the following, and also with reference to figures 1 to 3, the method for determining the control signal of the electromagnetic drive 20 of the interrupter unit 10 is described.
In figure 3 three diagrams show each the relative position 44 of the first arcing contact 12 and the relative position 46 of the second arcing contact 14 during the opening operation, in relation to their original closed position. The diagrams further show the corresponding distance 18 between the first 12 and second arcing contact 14 during the opening operation and also the fault current 48 - i.e. an alternating short circuit current 48. The x-axis 50 of figure 3 is a time axis.
In a first step of the method the control unit 22 receives the fault current signal from the sensing device 24. The sensing device 24 has generated the fault current signal by analyzing the alternating short circuit current 48 and has sent the fault current signal to the control unit 22. In a subsequent step, the control unit 22 determines the control signal of the electromagnetic drive 20 such that in a second timeframe 52 that occurs during opening operation and before the final distance 18 between the first and second arcing contact 12,14 is reached, the distance 18 between the first and the second arcing contact 12,14 is kept constant ± 20 %.
As can be seen by comparing figures 3a) 3b) and 3c), the alternating short circuit current 48 has a different value at the beginning of each diagram. Hence, also a duration 54 of the time during which the arc is burning, is different for each of the diagrams 3a), 3b) and 3c).
Figure 3c) shows the situation where the arc is extinguished at the minimum arcing time 56 the interrupter unit 10 can reach. Figure 3a) shows the situation where the arc is extinguished at the maximum arcing time 57, while figure 3b) shows an intermediate situation.
As can be seen in figures 3a) to 3c) the control signal is determined such that the second timeframe 52 starts at the minimum arcing time 56 of the interrupter unit 10. The minimum arcing time 56 the interrupter unit 10 can reach, is influenced by the geometry of the interrupter unit 10. With reference to figure 1 the control signal is determined such that the second timeframe 52 starts when the distance 18 between the first and second arcing contacts 12,14 is such that an insulating nozzle outflow limiting area 60 defined by the cross-section area of the contours of the diverging channel and the contour of the tip 42 of the plug contact 12 within the diverging channel is equal to or exceeds - and preferably exceeds by maximally 30% - a cross-section area 58 of the cylindrically shaped throat channel in the throat region 38. In other words, figure 1 shows the interrupter unit 10 in a situation when the second timeframe 52 starts.
As can be seen from figure 3, the control unit 22 is configured to determine the control signal, such that in the second timeframe 52 of the opening operation the motion of the first arcing contact 12 is essentially matched to the motion of the second arcing contact 14. Hence figure 1 also shows the interrupter unit 10 in a situation when the second timeframe 52 stops.
Furthermore, as can also be seen in figure 3, the control signal is determined such that the distance 18 between the first and second arcing contacts 12,14 in the second timeframe 52 does not correspond to the final distance 18 between the arcing contacts 12,14. Instead, the control signal is determined such that in a first timeframe 62 of the opening operation, wherein the first timeframe 62 immediately precedes the second timeframe 52 the distance 18 between the first and second arcing contacts 12,14 increases, and in a third timeframe 64 of the opening operation, wherein the third timeframe 64 immediately follows the second timeframe 52 the distance between the first arcing contact 12 and the second arcing contact 14 increases until the final distance 18 between the first arcing contact 12 and the second arcing contact 14 is achieved.
Furthermore, as can also be seen from figure 3, the control signal is determined such that the second timeframe 52 lasts until arc extinction of the longest arcing time 57 of the interrupter unit 10.
Fig. 4 schematically shows a diagram describing the relative positions 44, 46 of the first and second arcing contacts 12,14, and the corresponding distance 18 between the first and second arcing contacts 12,14 during the opening operation according to a further embodiment of the invention.
In this embodiment, the control unit 22 is configured to determine the control signal of the electromagnetic drive 20 such that in the second timeframe 52 of the opening operation the first arcing contact 12 and the second arcing contact 14 have no absolute motion. In this embodiment the electromagnetic drive 20 is not connected to the plug contact 12 as shown in figure 1 and 2 but to the tulip contact 14.
Figure 5 schematically shows in the upper half the flow streamlines 66 for a low current duty at current zero for the opening operation shown in figure 3 for the interrupter unit 10 of figures 1 and 2. The interrupter unit 10 is configured as self-blast circuit breaker.
In the lower half of figure 5 the flow streamlines 66' for a low current duty at current zero for a prior art self-blast circuit breaker interrupter unit 10' is shown. The prior art interrupter unit 10' performs a motion of the arcing contacts 12' 14' during opening operation where the distance between the first and second arcing contacts 12',14' is not constant within the second timeframe, but is continuously increasing.
As both halves of figure 5 refer to the longest arcing time, the position of the plug contact 12' of the prior art interrupter unit 10' is farther downstream in the diverging region 40' compared to the position of the plug contact 12 for the interrupter unit 10 according to a preferred embodiment of the invention.
The shaded area 68,68' in figure 5 indicates the regions of recirculating flow that are established in front of the plug contacts 12,12'. The arc extinguishing gas trapped in these fluid pockets is hotter than the arc extinguishing gas flowing outside of the regions 68,68'.
As can be seen in figure 5, the region of recirculating flow 68 68' is smaller for the interrupter unit 10 according to the preferred embodiment of the invention compared to the interrupter unit 10' according to prior art. This is because the arc extinguishing gas is accelerated by the smaller cross-sectional area 60 delimited by the plug tip 42 and the divergent contour of the diverging region 40 of the insulating nozzle 36. Reducing the size of the hot gas pocked 68 in front of the plug contact 12 results in a higher dielectric withstand capability of the interrupter unit 10, thus leading to an increase in the interruption performance of the interrupter unit 10.
While the invention has been illustrated and described in detail in the drawings and foregoing description, such illustration and description are to be considered illustrative or exemplary and not restrictive; the invention is not limited to the disclosed embodiments. Other variations to be disclosed embodiments can be understood and effected by those skilled in the art in practicing the claimed invention, from a study of the drawings, the disclosed, and the appended claims. In the claims, the word "comprising" does not exclude other elements or steps, and the indefinite article "a" or "an" does not exclude a plurality. The mere fact that certain measures are recited in mutually different dependent claims does not indicate that a combination of these measures cannot be used to advantage. Any reference signs in the claims should not be construed as limiting scope.

Reference signs list
10
interrupter unit
12
first arcing contact, plug contact
14
second arcing contact, tulip contact
16
switching axis
18
distance
20
electromagnetic drive
22
control unit
24
sensing device
26
nozzle system
28
heating channel
30
flow guiding direction
32
arcing region
34
auxiliary nozzle
36
insulating nozzle
38
throat region
40
diverging region
42
plug tip
44
relative position of first arcing contact
46
relative position of second arcing contact
48
fault current
50
x-axis
52
second timeframe
54
duration of arc burning
56
minimum arcing time
57
maximum arcing time, arc extinction of the longest arcing time
58
cross section area of channel in throat region
60
nozzle outflow limiting area
62
first timeframe
64
second timeframe
66
flow streamlines of arc extinguishing gas
68
regions of recirculating flow, hot gas pocket
1. Computer implemented method for determining a control signal of an electromagnetic drive (20) of an interrupter unit (10) for a high or medium voltage device, wherein the interrupter unit (10) comprises a first arcing contact (12) and a second arcing contact (14),
wherein for an opening operation of the interrupter unit (10) at least one of the arcing contacts (12,14) is axially movable along a switching axis (16) thereby bringing the first arcing contact (12) and second arcing contact (14) from a closed position with direct contact between the first and second arcing contacts (12,14) into an open position with a final distance between the first and second arcing contacts (12,14),
wherein the interrupter unit (10) comprises at least one electromagnetic drive (20) for driving the axial motion of the first and/or second arcing contact (12,14) from the closed position to the open position based on the control signal,
comprising the step of
- determining the control signal of the electromagnetic drive (20) such that in a second timeframe (52) that occurs during opening operation and before the final distance between the first and second arcing contact (12,14) is reached, a distance (18) between the first and the second arcing contact (12,14) is kept constant ± 20 %.
2. The computer implemented method according to any of the previous claims, wherein the step of determining the control signal of the electromagnetic drive (20) comprises determining the control signal such that in a first timeframe (62) of the opening operation, wherein the first timeframe (62) immediately precedes the second timeframe (52), the distance (18) between the first and second arcing contacts (12,14) increases, and in a third timeframe (64) of the opening operation, wherein the third timeframe (64) immediately follows the second timeframe (52), the distance (18) between the first arcing contact (12) and the second arcing contact (14) increases until the final distance between the first arcing contact (12) and the second arcing contact (14) is achieved.
3. The computer implemented method according to the previous claim, wherein the step of determining the control signal of the electromagnetic drive (20) comprises determining the control signal of the electromagnetic drive (20) such that in the second timeframe (52) of the opening operation the first arcing contact (12) and the second arcing contact (14) have no motion, or such that in the second timeframe (52) of the opening operation the motion of the first arcing contact (12) is essentially matched to the motion of the second arcing contact (14).
4. The computer implemented method according to any of the previous claims, the interrupter unit (10) comprises an insulating nozzle (36), wherein the insulating nozzle (36) comprises a throat region (38) and adjacent to the throat region (38) a diverging region (40), wherein the throat region (38) forms a cylindrically shaped throat channel and the diverging region (40) forms a diverging channel, wherein during opening operation a tip (42) of one arcing contact (12) first moves through the cylindrically shaped throat channel and afterwards through the diverging channel, and wherein the step of determining the control signal of the electromagnetic drive (20) comprises determining the control signal such that the second timeframe (52) starts when the distance (18) between the first and second arcing contacts (12,14) is such that an insulating nozzle outflow limiting area (60) defined by a minimum cross-section area between the diverging channel and the tip (42) of the one arcing contact (12) lying within the diverging channel is equal to or exceeds, and preferably exceeds by maximally 30%, a minimum cross-section area (58) of the cylindrically shaped throat channel, and/or
wherein the step of determining the control signal of the electromagnetic drive (20) comprises determining the control signal such that the second timeframe (52) starts at a minimum arcing time (56) of the interrupter unit (10).
5. The computer implemented method according to any of the previous claims, wherein the step of determining the control signal of the electromagnetic drive (20) comprises determining the control signal such that the second timeframe (52) lasts until arc extinction of a longest arcing time (57) of the interrupter unit (10).
6. Control unit (22) for determining a control signal of an electromagnetic drive (20) of an interrupter unit (10) for a high or medium voltage device, wherein the control unit (22) is configured to perform the method according to any of the previous method claims.
7. Interrupter unit (10) for a gas-insulated high or medium voltage device comprising
a first arcing contact (12) and a second arcing contact (14),
wherein for an opening operation of the interrupter unit (10) at least one of the arcing contacts (12,14) is axially movable along a switching axis (16) thereby bringing the first arcing contact (12) and second arcing contact (14) from a closed position with direct contact between the first and second arcing contacts (12,14) into an open position with a final distance between the first and second arcing contacts (12,14),
wherein the interrupter unit (10) comprises at least one electromagnetic drive (20) for driving the axial motion of the first and/or second arcing contact (12,14) from the closed position to the open position based on a control signal, and
wherein the interrupter unit (10) comprises the control unit (22) according to the previous claim.
8. The interrupter unit (10) according to the previous interrupter unit claim comprising a sensing device (24) communicationally connected to the control unit (22), and wherein the sensing device (24) is configured to generate a fault current signal based on analysis of a fault current (42) and to send the fault current signal to the control unit (22).
9. Interrupter unit (10) according to claim 7 or 8, wherein the interrupter unit (10) is configured such that for the opening operation of the interrupter unit (10) the first and second arcing contacts (12,14) are axially movable along the switching axis (16), wherein the electromagnetic drive (20) is connected to the first or second arcing contact (12,14) and drives the axial motion of said driving arcing contact (12,14) based on the control signal, wherein the interrupter unit (10) comprises a gear linkage mechanism connecting the motion of said driving arcing contact (12,14) to the motion of the other indirectly driven arcing contact (12,14), and wherein the control unit (22) is configured to determine the control signal, such that in the second timeframe (52) of the opening operation the first arcing contact (12) and the second arcing contact (14) have no motion.
10. Interrupter unit (10) according to claim 7 or 8, wherein the interrupter unit (10) is free of a gear linkage mechanism connecting the motion of one of the arcing contacts (12,14) to the motion of the other arcing contact (12,14), wherein the electromagnetic drive (20) drives the axial motion of the first and/or second arcing contact (12,14) based on the control signal, and wherein the control unit (22) is configured to determine the control signal, such that in the second timeframe (52) of the opening operation the motion of the first arcing contact (12) is essentially matched to the motion of the second arcing contact (14).
11. Interrupter unit (10) according to claim 7 or 8, wherein the interrupter unit (10) is configured such that for the opening operation of the interrupter unit (10) the first and second arcing contacts (12,14) are axially movable along the switching axis (16), wherein the interrupter unit (10) is free of a gear linkage mechanism connecting the motion of one of the arcing contacts (12,14) to the motion of the other arcing contact (12,14), wherein the electromagnetic drive (20) drives the axial motion of the first arcing contact (12) based on the control signal, wherein the interrupter unit (10) comprises a drive for driving the motion of the second arcing contact (14), wherein the motion of the second arcing contact (14) effects a pressurization of a pressurization chamber, and wherein the control unit (22) is configured to determine the control signal, such that in the second timeframe (52) of the opening operation the motion of the first arcing contact (12) is essentially matched to the motion of the second arcing contact (14).
12. Interrupter unit (10) according to claim 7 or 8, wherein the interrupter unit (10) is configured such that for the opening operation of the interrupter unit (10) the first and second arcing contacts (12,14) are axially movable along the switching axis (16), wherein the interrupter unit (10) comprises two electromagnetic drives (20), each connected to one of the arcing contacts (12,14) for driving the axial motion of the arcing contacts (12,14) based on the control signal, wherein the interrupter unit (1) is free of a gear linkage mechanism connecting the motion of one of the arcing contacts (12,14) to the motion of the other arcing contact (12,14), and wherein the control unit (22) is configured to determine the control signal, such that in the second timeframe (52) of the opening operation the first arcing contact (12) and the second arcing contact (14) have no motion, or such that in the second timeframe (52) of the opening operation the motion of one arcing contact (12,14) is essentially matched to the motion of the other arcing contact (12,14).
13. Gas-insulated high or medium voltage device comprising an interrupter unit (10) according to any of the previous interrupter unit claims, and wherein the high or medium voltage device comprises an arc extinguishing gas.
14. Gas-insulated high or medium voltage device according to the previous claim, wherein the gas-insulated high or medium voltage device is configured as a circuit breaker and more preferably as a puffer-type circuit breaker, or a self-blast circuit breaker.
15. Gas insulated high or medium voltage device according claim 13 or 14, wherein the arc extinguishing gas is selected from CO_2, SF_6, mixtures of CO_2 or SF_6 with a carrier gas and/or mixtures of fluoroketons and/or fluoronitriles with a carrier gas.
HD 41621/GQ
EP
22203642.8
Hitachi Energy Switzerland AG
1
DH
20230405
H01H
WO
9528025
A1
ABB POWER T & D CO [US]
19951019
X
1-3,5-15
Y
4
* page 1, line 21 - line 27 *
* page 3, line 15 - line 35 *
* page 15, line 15 - line 35 *
* page 29, line 31 - page 31, line 5 *
* figures 2, 3, 5 *
WO
2015111919
A1
ILJIN ELECTRIC [KR]
20150730
Y
4
* figure 1 *
US
6023404
A
MARMONIER JEAN [FR]
20000208
Y
4
* column 2, line 31 - line 52 *
* column 3, line 16 - line 30 *
* figure 1 *
Fribert, Jan
The Hague
20230328
WO
9528025
A1
19951019
US
5629869
A
19970513
US
5636134
A
19970603
US
5638296
A
19970610
WO
9528025
A1
19951019
WO
2015111919
A1
20150730
NONE
US
6023404
A
20000208
AT
E262215
T1
20040415
CA
2238903
A1
19981204
CN
1201150
A
19981209
DE
69822365
T2
20050217
EP
0883145
A1
19981209
ES
2216254
T3
20041016
FR
2764431
A1
19981211
ID
20418
A
19981210
US
6023404
A
20000208